Cause of the issue was short in low voltage wiring going to outdoor coil. Replaced section of damaged wire. Short also damaged thermostat and wouldnâ€™t being on AC. Replaced thermostat. System was also 1 lb low on R-22 and had a very weak capacitor on outdoor coil. Replaced capacitor. System is operating normally at this time.