Complaint no cool in office Changed a fan capacitor and got fan motor running. It may still go bad we will see. It ran fine for the entirety of my time spent here after that. Unit was flat out of refrigerant. Pressurized unit and conducted leak search. Determined leak was coming from a rupture in discharge line, repaired leak and charged unit with 8.5 lbs of 421A. Unit cooling at this time.