Charlie’s does a great job and I appreciate how thorough they are with their work.
Excellent service! Courteous, very kind and fixed the problem quickly. Thank you so much!
Shawn was very personable and did a thorough job checking over the unit.
Thorough, professional, and polite.
Great customer service!
Reliable, on time and thorough. No surprises.
Always great efficient service
Justin was here early Monday morning to replace our fan motor. He was very competent, a hard worker, and had the necessary parts on his truck, pp
Saturday morning of the great heatwave our ac started to faulter. Within minutes of leaving a message, Charlie’s Air and Heating on-call technician returned my call and was at my door within 30 minutes. He quickly diagnosed the problem and had the necessary parts on his truck to do the repairs. Great service! Thank you!
Heating Maintenance PCS 2023 Heating Check Up Prepaid. System is heating at this time, all drains and hoses are clear, CO levels have been checked for a second time on 10/2/23 and are good. CO detectors have been installed through the home.
2023 Fall Check Up PCSA Prepaid Cleaned ice machine. Cleaned flame sensor. Checked wire connections. No CO detected. Replaced filters. All 3 systems were operating normally. Pastor had us look at systems for east and west Classrooms off the Fellowship Hall. West System had a bad thermostat that would shut off the AC. Replaced thermostat. System may need inspected after it’s had a chance to thaw. East System appears to be operating normally. Could be a programming issue with the thermostat but it appears to be operating normally. Noticed several wires going to the outdoor coils heavily damaged by weed trimmer. Sealed wires going to units and secured them to copper line sets.
Completed heating maintenance, cleaned coils, flushed drain, replaced filter, checked air temps, checked blower and electric heat amps, checked heat pump in cooling mode and found no issues, checked capacitor, made sure system is working properly System is cooling at this time
2023 PCSA Heating Check Up Renewal Heating Maintenance. System is heating efficiently at this time, all drains and hoses are clear, flame sensor has been cleaned, CO has been tested and levels are acceptable, and temperature rise is good. Filter isn’t clean at this time, I would check it in 1-2 months.
2023 heating check up
2023 PCSA Heating Check Up prepaid Heating Maintenance Completed heating maintenance, cleaned flame sensor, cleaned inducer drain, customer wants to change filter in Spring maintenance, checked air temps, checked blower and inducer amps, checked blower capacitor, checked gas pressures, checked igniter resistance, made sure system is working properly System is heating at this time
2023 PCSA Heating renewal Heating Maintenance. System is heating efficiently at this time, temperature rises good, filter has been replaced, and all hoses and drains are clear.I did not see a carbon monoxide detector anywhere in home, if there isn’t one I would recommend getting one. We can provide, install and test one if needed for home. Hot surface igniter is also showing signs of potential failure. If desired, we can replace this part as a preventative. Other than this, system is heating well.
Heating Maintenance PCSA 2023 Heating Check Up Renewal Replaced filter in attic. Cleaned coils. Checked charge. All operations good.
Completed heating maintenance, cleaned flame sensor, vacuumed drain, replaced filter, checked air temps, checked blower and inducer amps, checked gas pressure, checked blower capacitor, checked igniter resistance, made sure system is working properly System is heating at this time
Heating Maintenance PCSA 2023 Heating Check Up Renewal System is heating efficiently at this time, drains and hoses are clear, flame sensor is clean, and CO detector has been tested.
2023 heating maintenance
Condensate pan cracked. Customer will decide what they want to do. They make take a season to think about it. Quoted 840 for the pan replacement
Estimate for a new heat pump install.
No AC- System had a bad condenser fan motor, replaced motor and capacitor and verified operation of system. System is cooling efficiently at this time.
Heating Maintenance PCSA 2023 Heating Check Up 2 Systems Renewal added 1 lb of 410A to older trane system on main house. Brought two filters and replaced current filter. Replaced high pressure switch on york for add on.