Awesome, expert service. I never allow anyone but Charlie’s to service my heating/cooling equipment.
Complaint no heat, unit was locked out on a code 7. Cleaned flame sensor, checked and adjusted gas pressure, was at 2.4â€. Cleared code, cycled furnace, system is heating
Complaint a/c is freezing up I warned customer that this thing doesnâ€™t have long. Head pressure way up at 400. Most likely embedded coil or impending load failure or both Unit is cooling at this time after adding 1 lb of r-22
Complaint unit short cycling Cause of the issue was bad thermostat. Replaced thermostat. System is operating normally at this time.
PCSA 2021 a/c maintenance prepaid . Cleaned condenser removed side panels &washed. Cleaned drain.
PCSA 2021 RENEWAL AC MAINTENANCE Equipment in system Filter changed provided by homeowner Drain flushed Target of 18 degrees +/- 5 SH of 14 degrees All checks good Mrs. Jackson will stop by the office and pay her bill
Outside unit not coming on Bad cap Unit now cooling
2021 a/c only check up renewal Need to come back and check charge Thermostat will not close due to low house temp and wall placement
PCSA 2021 2 system a/c check up prepaid Monitor contactor, suggested replacing but Paul is hoping to move soon Changed filter downstairs
Complaint no heat. Board 3310301000
Flue issue took of plug to get unit to run metal roof need 2 guys to rod out consentric flue cap.cleaned out intake 1 3â€ coupler
No heat filter was clogged from foundation work. Rose left to get a filter. Signed up on service agreement, cleaned furnace system is heating
Complaint no heat replaced t-stat 8444
2020 Fall PCSA Prepaid Everything was clean and operating normally at this time.
2020 Heating Check Up Renew & Scheduled 10/30/20 2021 AC Check Up Included
Bad thermostat. Replaced stat checks good