Installed two new York heat pumps on a new construction job
PCSA 2021 AC Check Up Found leaking valve core on liquid line. Replaced core and added 3 lbs of R-410A. Also replaced contactor on outdoor coil. System is operating normally at this time. Everything else was clean and checked out well.
Start PCSA 2021 AC Check Up Changed outdoor cap Charged unit with 4.5 lbs of R22 Filter is clean Customer will decide whether he needs an estimate from Pete
Install: 2 1/2 Ton 15.75 SEER York LX heat pump 3 ton York LX series air handler Freon Lines 5â€ Filter WARRANTY: 10 years Parts, labor and Freon #charlie
Quote for 2 1/2 Ton 17 SEER York heat pump and York electric furnace
Complaint: No Heat Downstairs unit. Replaced blower motor 1 of 3 heaters work . No R-22 in unit. Set up est. Customer installing new heat pump
Estimate for new heat pump system
2020 Fall pcsa check up, tested electric heat, heat pump, everything checks out great, Linda just changed filter herself last week
2020 PCSA Heating Check Up Prepaid changed filter customer supplied, everything running great
Filter 20x20x1 small for 3 1/2 ton .multiple returns donâ€™t draw well 3 of 4 heaters hooked up ok.
Puron levels were a little off. Want to monitor during AC check up to see if the cause is a leak or a failing txv. System also needs new contactor during next check up. Everything else was clean and checked out well.
Daniel picked up 9/3/20 Complaint was compressor kicks off in a few seconds . Dropped back off 9/11/2020
PCSA Spring 2020 AC Check Up Renewal $165.00 Fall 2020 Heating Check Up Included Flushed drain, replaced filter customer supplied, inspected all electrical, checked charge system is cooling
No AC Compressor grounded spoke to Linda, she would like a new unit Linda (ours) will call to get her financing
Most likely cause of the issue is weak breaker in electric panel upstairs. Customer will replace breaker and let us know if it continues. Contactor may need replaced next check up. System is operating normally at this time.