Estimate for new unit and duct work.
Cause of the issue appears to be the control board inside the furnace. The plug on the board is coming detached causing the board to not recognize the rollout switches. Customer wants a price on a new control board. Customer may also want a price on a new system and duct work.
2023 Fall Check Up PCSA New No heat. Cause of the issue was a dirty flame sensor. Cleaned flame sensor. Checked wiring. Burners are a little dirty but operating normally. Condensate pan gasket is beginning to leak and could present problems in the future. Replaced filter. No CO detected inside the house. System is operating normally at this time. Customer may want a price on a new system and some duct work in the near future.
Cause of the issue was a bad outdoor capacitor. Replaced capacitor. System is operating normally at this time.
Cause of the issue is a bad capacitor and a burned wire. Both will need to be replaced for system to work normally. Cost of the capacitor would be $151.