As always as always excellent excellent
GREAT SERVICE AS ALWAYS
Charlie’s Heating and Air have the best customer service and technicians, hands down! Daniel and Phil are knowledgeable, kind and take time to answer any questions. Charlie’s is always on time and if they are running behind, they will inform you by text message when they are on the way. We will ALWAYS recommend Charlie’s!! Very thankful for them and their work ethic!
Checks good on all furnaces. Screens have been removed from flues. Gas pressure set correctly on York All hoses and drains vacuumed out Temp rises and CO levels check good. All filters were changed and provided by customer No pressure switch issues on left sanctuary furnace Sensors cleaned All capacitors check good
Fix TXV in guest house . Reorder A/coil & TXV. Replaced A/coil &TXV.
Leaking from txv flare. Steve is going to come out and see what he can do. I have removed diag for now
2021 PCSA a/c maintenance prepaid All checks good Replaced filter
Replaced indoor coil at guest house, pressure tested with 200 psi nitrogen for 30 mins, evacuated to 500 microns, started and charged unit, remade drain line, tested full operation system is cooling at this time
2021 PCSA a/c check up renewal
Stuff in orifice on #1  burner cleaned out ckd gas pressure
AC PREPAID CHECK UP . Leak not resolved on new unit. Needs price on A/ coil for rental.
PCSA 2021 AC Check Up Renewal completed pm on 4 A/c units. All ck. Ok, changed filters as needed provided by customer
PCSA 2020 Heating Check Up Renew Little over on charge. 475 on a 36 degree day with a discharge temp of 167 reduced to 425 psi and 143 degree discharge. All checks good. Changed filter
2020 PCSA Prepaid Check Up. Need parts for both humidifiers will quote.replaced parts
PCSA 4 Systems 2020 AC Check Up Renew & Done 5/13/20 2020 Heating Check Up Prepaid & Scheduled 10/13/20 Left furnace in church cannot get pressure switch tthe close by natural means. Need to come back. Trane m# tux100c948d1. S# 251snmk7g
Ckd system all in good order, cut drain and flushed very long run.
PCSA Spring 2020 AC Check Up Fall 2020 Heating Check Up Included Blower capacitor and capacitor on outdoor coil needed replaced. Everything else was clean and checked out well.
Quote for 2 1/2 ton 16 SEER York Heat Pump