Steve was on time, informative, thorough and very professional
Would like to be in a commercial for you and share my experience!!
Technician was on time, very knowledgeable, safety conscious including precautions for COVID. He was willing to answer questions and very neat in completing his work.
PCSA 2021 heating maintenance free w/ install All electric heat coming on cust,er provided filter left Over from install all checks in air conditioning mode good 20 degree drop Updated filter size
Gave quote to insta dual fuel system
Gave quote for new AC unit and air handler
Giving price to replace Intertherm AC unit with York 3 ton 13 SEER air conditioning unit with 10 year parts and labor warranty
Replaced indoor TXV 1 yr parts & labor
PCSA 2021 PREPAID AC CHECK UP Subcooling seemed a bit unreasonable at 22 degrees Unit says target of 10 from manufacturer Took a littl gas out for a total of 14 degrees subcooling All other checks good filter is clean
PCSA 2021 PREPAID AC CHECK UP
Complaint AC Freezing Up System low on freon added 2# R-22
PCSA 2021 AC Check Up Free w/ Install
Complaint unit making noise . No issues found replaced filter customer stock.
Customer Complaint is the thermostat showing its 77 but cold in house sometimes. Found supply air vent blowing warm air on thermostat causing system to short cycle. Set chair over vent and returned to see if problem was any better. Customer purchased service agreement
Water in inducer needs flue tee. Ck warrantyâ€™s.
Rewired elec. furnace. All 3 heaters work. A/c working. Please bill customer.
Sold 15 SEER York LX series heat pump and electric furnace. Replace freon lines and add 5” air filter
System is a pound or 2 low on R-22. Customer would like estimate on new system.