Daniel was very thorough. He checked everything, and cleaned the drain lines. We were very satisfied with the service we received today.
Great service! Steve was very thorough & explained all that he checked.
I give u guys A for good service
Very nice young man very professional and polite.
Limit switch on system # 1 is getting weak and may need replaced in the future. Transformer on system #9 is getting loud and may need replaced during a future check up. - Daniel South pack flame sensor is starting to loosen in fixture and was off by a quarter turn. Was causing loss of flame. Cleaned and adjusted and fired 3 times belts and filters should be replaced next visit - Shawn
Completed fall ck, flame sensor starting to pit
PCSA 2021 a/c maintenance free w/ install Everything was clean and checked out well. System is operating normally at this time.
Changed 20x25x5 filter & cleaned condenser
Thermostat is making a clicking noise. 10 Year Parts & Labor . Replace8463 bedroom
No cooling found unit out of gas, compressor blew out terminal. Spoke to John, need to figure out pricing. Let him know tenant has no ac 7/20 returned, pulled metering device, flushed lineset and both coils. Installed new compressor, capacitor, contactor, washed indoor coil and hit with self rinsing cleaner. Replaced filter drier, pressure tested, evacuated to 500 microns, added 6 lbs r22 replaced filter system is cooling
2021 PCSA a/c maintenance renew annual pay
PCSA 2021 PREPAID AC MAINTENANCE
Thermostat is acting strange at times. May need replaced during a future check up. Everything else was clean and checked out well. System is operating normally at this time.
System #6 had a small leak at a solder joint. Repaired leak and recharged system. System number #10 in chapel had a bad thermostat and the disconnect to outside unit was off. Replaced thermostat and checked charge. System #3 in nursery was 2 lbs low on R-22. All three systems are operating normally at this time.
Quote to replace 3 ton heat pump
Giving quote to replace 3 ton Trane heat pump with York 3 ton 16 SEER heat pump
2021 AC Check Up Prepaid Everything was clean and checked out well. System is operating normally at this time.
2021 2nd Quarter Preventive Maintenance Washed Condenser coil and Replaced Filter
Installed: 1 - York 60,000 BTU 95% Efficient Furnace Mod# TM9E060B12MP12 Ser# W2K0154586 1 - York 2 1/2 Ton 16 SEER AC Unit Mod# YCG30B21S Ser# W2C1829852 1 - York Evaporator Coil Mod# CF36BXA1 Ser# W2N0558658 Freon Lines PVC Flue Piping 16x25x5 Filter Hooked To Existing Duct , Wiring and Piping Warranty: 10 Year Parts, Labor and Freon Comfort Plan# 1 Year PCSA Maintenance (Fall 2021 Check Up & Spring 2022 Check Up Included) **Customer will receive a check for $300 by mail in 4-6 weeks from York Rebate**