Daniel was very thorough. He checked everything, and cleaned the drain lines. We were very satisfied with the service we received today.
Great service! Steve was very thorough & explained all that he checked.
I give u guys A for good service
Very nice young man very professional and polite.
Quote to replace 3 ton heat pump
Giving quote to replace 3 ton Trane heat pump with York 3 ton 16 SEER heat pump
2021 AC Check Up Prepaid Everything was clean and checked out well. System is operating normally at this time.
2021 2nd Quarter Preventive Maintenance Washed Condenser coil and Replaced Filter
Installed: 1 - York 60,000 BTU 95% Efficient Furnace Mod# TM9E060B12MP12 Ser# W2K0154586 1 - York 2 1/2 Ton 16 SEER AC Unit Mod# YCG30B21S Ser# W2C1829852 1 - York Evaporator Coil Mod# CF36BXA1 Ser# W2N0558658 Freon Lines PVC Flue Piping 16x25x5 Filter Hooked To Existing Duct , Wiring and Piping Warranty: 10 Year Parts, Labor and Freon Comfort Plan# 1 Year PCSA Maintenance (Fall 2021 Check Up & Spring 2022 Check Up Included) **Customer will receive a check for $300 by mail in 4-6 weeks from York Rebate**
Quote for 95% Furnace and 16 SEER York air conditioning unit
All air conditioning systems check good in cooling still need a 24x24x2 for system #4 win air was out when I checked. All air filter sizes recorded in folder
Added 2 lbs of freon, AC unit was low. Did not put any refrigerant last year.
Customer has part in needs installed and ice machine cleaned . Cleaned ice machine installed part. All material provided by customer.
Condenser Coil Cleaning, AC Maintenance & 20x25x5 Filter Change ....As Per Quote
PCSA 2020 Heating Check Up Checked electric heat, inspected all electrical, checked filter, tested heat pump, checked charge, tested defrost system is heating
PCSA 2020 Heating Equipment Maintenance RENEWAL PCSA 2021 Cooling Equipment Maintenance Included Filters are changed by customer
2020 Fall PCSA Renew Customer would like 4 filters every spring check up. Everything was clean and operating normally at this time.
PCSA 2020 Heating Check Up ckd system cleared codes on board. New filter
Everything was clean and checked out well.