I woke up hot and sticky yesterday so I called the gang down at Charlie’s. Daniel came straight over and got my apartment cooled down…….but not me! After he had been bent over by the furnace for awhile, it took a glass of lemonade to cool us both down. Daniel was there all afternoon servicing my needs and then some. He is a very thorough and thoughtful young man. I would highly recommend him to all my gals. Sincerely, Phyllis
During System maintenance found Carbon Monoxide in flue pipe over 100 ppm. Flue CO levels were much higher than last heating check up. To rule out improper fuel/air mixture we checked flues for obstructions in flue piping and cleaned burners. CO levels were still high. CO due to cracked Heat exchanger. Furnace replacement needed.
PCSA 2021 RENEWAL - Heating Check Up Tested electric heat, checked all connections, tested fan, cleaned air handler, cleaned filter, vacuumed return, tested heat pump, checked charge, system is working great
Filled out form.
Unit Frozen Up Unit satisfied at 69 upon arrival very dirty filters, removed, checked charge system is cooling, tenant will get new ones
Quote for new system
Water in floor 2021 Spring AC Check Up PCSA Cause of the issue was clogged drain line. Everything else was clean and checked out well. System is operating normally at this time.
PCSA 2021 RENEWAL - AC Maintenance
Unit Frozen Up 2021 Spring PCSA AC Check Up Cause of the issue was bad blower motor. Replaced blower motor. (Parts Warranty) Everything else was clean and checked out well. System is operating normally at this time.
Freezing up inside Checked on systems at 201 and 203 Rawley Brooks. 201 needed new air filter and 2 lbs of R-410A. Blower motor speed may need turned up in the near future. 203 was 4 lbs low on R-410A. Both systems are working normally at this time.
Gave price for new LP gas furnace
PCSA 2021 AC Check Up Prepaid Flushed drain line, inspected electrical, cleaned filters, checked charge system is cooling
2021 PCSA AC ONLY Check Up
No heat fixed short in w2 wire outside, took off nest thermostat and installed the old one. Tested electric heat, heat pump and ac.
Replaced burner throat plate
Plugged filter unit running on limit . Reset ckd. Unit new filter cust. Stock