PCSA 2021 AC Check Up Prepaid Flushed drain line, inspected electrical, cleaned filters, checked charge system is cooling
2021 PCSA AC ONLY Check Up
No heat fixed short in w2 wire outside, took off nest thermostat and installed the old one. Tested electric heat, heat pump and ac.
Replaced burner throat plate
Plugged filter unit running on limit . Reset ckd. Unit new filter cust. Stock
No heat found 2 out of 3 elements burned up, a bad limit and a bad sequencer. Need to get a new heat kit. Was able to get one element to come on, house was heating up when I left. Also replaced filter, was very dirty. Replaced heat strips, sequencer and limit run check ok
Rachel had found a piece of paper in the blower, it was a sticker that had pulled off motor housing. Tested heat pump and electric heat, sounds great. There were extra wire nuts in the unit put them with the baggy next to the furnace. Everything looks great
No heat found system cycling on dirty flame sensor. Cleaned sensor, also cleaned drains and pressure tubes, cycled furnace itâ€™s operating fine now
Did heating check up there were questions about the x13. Checked unit, tested blower in heating, cooling and fan on. Sounded like the problem had been a tripped limit. Checked charge, inspected filters customer will change them
Replaced 2 stack sequencer
PCSA Fall 2020 Heat Pump Check Up Spring 2021 Included Tested electric heat, inspected electrical, checked proper heat pump operation, defrost operation, cleaned filters, checked charge everything checks out great system is heating
Replaced outdoor unit, pressure tested to 200 psi for 30 mins, evacuated to 500 microns, added 5 lbs 3 oz r421a charged to 15 degrees superheat system is cooling
Found at least one more leak in outdoor coil.
System operating normally upon arrival. Freon levels look good.