2022 Spring Check Up PCSA New System inspection. Replaced filters. Flushed drain line. Capacitor on blower motor was weak and heavily corroded. Capacitor on outdoor coil was getting very weak. Replaced both capacitors. Thermostat display was struggling to show correct temperatures. Replaced thermostat. Disconnect on outdoor coil was damaged at one point but is operating normally. Would recommend replacement during future check up. Everything else was clean and checked out well. System is operating normally at this time. Customer wanted to sign up for service plan.