Complete explanation of service performed and operation of unit. Wonderful technician. A +
Very pleased with the care call!!!
Phil, the technician, observed the failed air supply dryer equipment, and through a series of steps, diagnosed the problem, and then brought the equipment back on-line in a one, two, three type step of workmanship process. Thank You Phil for getting our critical air supply equipment back in operation again.
He explained everything thoroughly. Was very friendly. Price was great. Service was 10 out of 10. Wouldn't even consider going anywhere else. We are lifetime customers!
Phil has always explained how to run our system as efficiently as possible. When he notices something not right, he explains when it might need replacing and why.
Shaun is a very dedicated worker who focused intently on the job.
Phil did a great job wonderful communication
We love Shawn he does an excellent job and explains everything so well. We can always count on Charlie's
Found gas valve off checked co in room 0 ppm . Copper gas line to furnace & water heater replace with new when system replacement
Relay & used t-stat
Renewal PCSA 2021 heating maintenance . Completed fall Pm unit in good order..
PCSA 2021 heating maintenance prepaid . Completed fall Pm new filter washed filter to dehumidifier.
Turned on gas 10 yr p&l
Complaint no heat Cause of the issue was furnace water had leaked onto one of the terminals for one of the furnace limits. Repaired terminal and vacuumed out drain trap inside furnace to try to prevent problem from reoccurring. System is operating normally at this time.
2021 Fall furnace maintenance PCSA Performed furnace check up. Lennox still has cracked heat exchanger and will need replaced in the future. Everything else was clean and checked out well. Systems are operating normally at this time. Vent hood motors are well oiled and operating normally as well.
PCSA 2021 heating maintenance renewal Replaced condenser fan motor (parts warranty). Everything else was clean and checked out well. System is operating normally at this time.
PCSA 2021 heating maintenance prepaid .completed PM
Heating Prepaid Maintenance. Completed fall ck. Look at blower in spring after cking Freon.
Cleaned unit replaced condenser motor & capacitor 10 yr. P&L
Complaint a/c not keeping up, checked charge, found unit low on r22. Added 1 lb, checked airflow, consistent temps from each vent. Explained situation to tenant, she will call if thereâ€™s any issues. We dropped it from 78 to 73 in the house while I was there. We were out early summer, hasnâ€™t worked right since then. No diagnostic charged
2021 PCSA Heating Maintenance Renewal and (2) 16x25x5 Filters. Completed pre-paid maintenance. New filter and left spare . Set hi &low gas psi. No codes on board, extended flower run time.
Everything was clean and checked out well. System is operating normally at this time.
Washable filters ok ck cap. Unit in ok condition