Super good and fast
Above and beyond excellent service
Great job as usual.
Charlie’s very professional team
Pete was very informative about a new heating and air system. He has given me good options to choose from.
Very friendly and courteous great job
A big thank you to Charlie’s for repairs to our air-conditioning unit that is very old and helping us to get some air while we contemplate buying a new system. Our technician Daniel was very personable and helped us and was very knowledgeable about our system and what we needed to do to get the best out of it thank you very much we will recommend Charlie’s.
Very good technician and service
Quote furnace board blower cleaning start PCSA. Bypassed blower constant run.
PCSA 2022 a/c check up renewal All checks good changed filter recommended pleated
PCSA 2022 AC Check Up Free w/ New Install. System checks out good and running efficiently, filter is changed and provided by customer, outdoor condenser coil was very dirty and is now cleaned, and drain is flushed.
Both systems are running efficiently at this time, drains are clean, outdoor condenser coils are clean, and filters are changed. Temperature drop is acceptable and refrigerant pressures looks good.
PCSA 2022 a/c check up. System checks out good and is running efficiently, filter is changed, outdoor coil is clean, and drain is clean. Outdoor capacitor was getting weak and causing system not to run at full potential, changed out and verified operation.
Complaint water spot on ceiling. Found that customer had water draining from emergency drain due to clogged main drain, emergency drain was also clogging up. Flushed both drains thoroughly and verified drainage. Customer also had 10% off service agreement coupon. Signed up for maintenance to make sure we stay on top of system now that it’s starting to show signs of age.
2022 Spring Check Up PCSA Renew Everything was clean and checked out well. System is operating normally at this time.
PCSA 2022 FREE WITH INSTALL AC CHECK UP. Completed Spring Pm unit in good order. Painted muffler, moved capillary tubes.
PCSA 2022 a/c check up 2 system renewal. Unit #324- 1 R-22. Duel capacitor. Has small noise in blower motor on start up, not currently an issue. Unit # 422 - Duel capacitor filter
PCSA 2022 a/c check up prepaid. Completed Spring Pm unit in good order. Painted muffler. Filter ok.
Unclogged drain added a lb of 22
Cause of the issue was dead blower motor. Replaced blower motor and system appears to be operating normally at this time. Filter grill needs cleaned and filter needs replaced. Customer will take care of that in the near future.
Water coming thru ceiling. Unit in Attic. Cause of the issue was too extreme of a pitch in the drain line which was causing the line to clog. Lowered drain line slightly and thoroughly flushed drain line. System is operating normally at this time.
PCSA 2022 PREPAID AC CHECK UP. Completed Spring Pm unit in good order. Hooked up common wire to t-stat.
Complaint no heat . Too warm in house to bring on heat, jumped t-stat cycled unit. Unit in poor condition will need work this winter.