Excellent Workmanship!!! Great Service along with a very competitive price for the service performed.
Response from Charlie's Air Conditioning & Heating:
Thank you for taking the time to write a review! We appreciate you!
Daniel is great to deal with. Personality is tops. Very friendly and informative.
VERY ACCURATE, FRIENDLY AND PROFESSIONAL!!!!! BEST DECISION OUR FAMILY HAS MADE FOR OUR HOME HEATING & AIR!!!!!!!
Very friendly & professional! Excellent job knowledge! Appreciated walk through of both units serving and explaining importance of routine maintenance.
Shawn C did an excellent job as does everyone at Charlie's A C and heating
I would recommend Shawn--he did excellent job for me.
Wonderful person who was very helpful and answered all my questions.
The tech was very professional and did a great job !
HVAC Repair Furnace Diagnostic Thermostat was going bad, replaced and verified operation of system.
Heating Service Furnace Service Maintenance PCSA 2023 Heating Check Up Renewal. System’s are heating efficiently at this time, filters have been replaced. Contactor for downstairs heat pump was failing, replaced and verified operation.
2023 heating maintenance
2023 PCSA Heating Check Up Renewal Heating Maintenance. Filter is clean and system is heating efficiently
Heating Service Agreement HVAC Service PCSA 2023 Heating Check Up Prepaid Completed heating maintenance, cleaned flame sensor and burners, vacuumed drain, filter is provided by customer, checked system operation and found no issues, made sure no gas leak is present, made sure system is working properly System is heating at this time
2023 PCSA Heating Check Up Prepaid Heating Service Agreement HVAC Service Checked wire connections. Filter was replaced recently. Thermostat is operating normally. Burners are clean. Cleaned flame sensor. Everything was clean and checked out well. System is operating normally at this time.
Found and replaced bad relay board for confirmation of closed overhead door. Labor included in price of relay board for gas furnace set up. 1 hour of labor charged for diagnostic work on 480 electric heater. Found bad thermostat which must be replaced. Upon returning I will replace thermostat for southeast and northwest electric heaters for building 2. Will also permanently wire around indoor ambient sensor for south east electric heater.
Heating Service Agreement HVAC Service PCSA 2023 Heating Maintenance 2 Systems Free w/ Install York & Mitsubishi Unit All operations checks good customer will take care of filter when replacement time comes.
Heating Service Agreement HVAC Service 2023 PCSA Heating Check Up Renewal System is heating at this time, filter has been changed.
Converted Dectron to new components. Replaced primary control board, controller and duct mount sensor. Installed fan and heat controls in pool room per Phil for convenience. Tested operation of all components, all tests show that this was a successful conversion. Went through operation with Phil, job is complete
2023 PCSA Heating Check Up Renewal HVAC Service Heating Completed heating maintenance, filters are provided by customer, flushed drain, checked system operation in cooling and electric heating mode and found no issues, made sure system is working properly System is cooling at this time
2023 Fall Check Up Checked wire connections. Cleaned air filter. Heat strips are operating normally. Blower is operating normally. Thermostat is operating normally. Defrost mode is operating normally. Puron levels are within range. Fixed rattling fan guard. Disconnect on outdoor coil may need replaced in the future. Everything was clean and checked out well. System is operating normally at this time.
2023 PCSA Heating Check Up Heating Maintenance. Everything checks out good on the gas side. Heat pump however is low on refrigerant due to a leak that i confirmed on the indoor coil. We will get back with a quote for replacement indoor coil.
Estimate for install of gas furnace and air conditioner
Diagnostic HVAC Service Furnace Service Complaint no heat nothing coming on. Cause of the issue was a dead igniter. Replaced igniter and tested system operation. System is operating normally at this time.