Steve was awesome. The Beagles approved his work.
Steve was absolutely great. He was very knowledgeable and genuine. He was on time, polite, and took the time to answer my questions and explain his work.
Shawn has been here twice. He is very personable and very knowledgeable.
Daniel Butts is out typical service guy who comes out to the house. He is wonderful! Very nice, and does a great job with any inspections or repairs. I wouldn’t go with any other company besides Charlie’s! Also our dogs love Daniel. 🙂
2021 Spring pcsa, flushed drains, checked filters, inspected electrical, washed condensers, checked charge, both systems working great
PCSA 2021 a/c check up prepaid Flushed drain, flushed condensate pump, checked charge, cycled ac, replaced outdoor capacitor, system is cooling
No cool, fired up system upon arrival, everything running good. Checked charge, inspected electrical, watched system operate for 15-20 mins, everything looked great. Told them Iâ€™d be in Carbondale all day, call if it trips out today and I can come back over
PCSA 2021 AC Check Up Free w/ Install Inspected indoor unit, replaced filter, inspected condenser, cycled ac, checked charge system is cooling
PCSA 2021 AC Check Up Flushed drain, it was backed up, checked filter, inspected all electrical, washed condenser, checked charge, outdoor capacitor reads bad
PCSA 2021 AC Check Up Renewal. New filter ckd unit removed plastic mesh. Unit in ok condition.
Complaint blower doesn't always shut off when emergency heat turns off. Blower set to 5 & 1. Adjusted program so itâ€™s not so aggressive. Gene is going to watch system operation
No heat no a/c. Frequecey drive blower not running. Broken filter door Handel removed bolt need to retapp or replace. Found unit has low ambient protection, set to 55 degrees
Outside unit making lots of noise switched to emergency heat want outside unit checked out to make sure no damage Found outdoor fan motor squealing, locks up then starts again. Need to replace motor, ordered motor.replaced condenser mtr. Down stairs unit.
2020 heating check up PCSA free w/ install Install looks great Replaced filter with leftover from install All checks good
Called Wrong Company
No Heat Dr Ripperda's side No heat found bad gas valve coil, it didnâ€™t open the valve every time. Replaced valve, tested heat, ran it from 70-74 system is heating
No Heat CO in house boiler system Took apart and redid gas line connections from both unions to where main line comes into the house. Several connections had no pipe dope, some were hand tight. Ameren gas guy on his way out to check for leaks, coming back tomorrow afternoon to clean boiler and test system Returned next day, cleaned boiler as best I could, replaced rotted flue pipe, redid gasket on burner box, tested heat, shuts off and turns on correctly, checked co readings in and around flue and boiler system is heating correctly
Installed 3 iwaves, coming back tomorrow to install the rest Installed 6 iwaves on roof
Installed Air Scrubbers