Great job. Very professional.
Heat Pump Repair Complaint: Unit freezing up. Turned down blower speed to help with temperature rise. Also removed 1 lb of R-410A to help compensate for blower adjustment. Temperature rise was at least 21 degrees. Puron levels appear to be normal. Checked both ambient and defrost sensors to make sure they were reading correct temperatures. Both seem to be operating normally at this time.
Furnace Repair Complaint: Furnace not always coming on. Cause of the issue was dirty burners. Cleaned burners and flame sensor. Furnace appears to be operating normally. Humidifier needs a new pad when possible.
Adjusted charge to have pressures operate normally. System is operating normally at this time.
Heating Repair - Limit error recorded, temp rise looks high in low fire, adjusted blower speed up one in low fire. Temp rise now at about 50 degrees in low fire. Unit heating at this time. Codes cleared
Replaced limit, turned off breaker and capped wires coming from the breaker with the 10 gauge wire. Started heat, everything is working correctly
PCSA 2022 a/c check up prepaid replaced panel on outdoor cond. coil
Complaint No Heat - Unit not coming on and performed the 2022 Heating Maintenance All maintenance performed. Heat pump not showing any issues at this time. Brad will monitor. Had a filter for the house but not for the barn. Barn filter is dirty and still needs replaced. All checks good on both furnaces and heat pump
Gave quote for 3 ton heat pump installation
AC Check Up cleaned condenser, flushed drain, inspected all electrical, replaced bad dual capacitor, checked charge, system is cooling. Need to come back with a filter
Replaced bad blower capacitor . Unit in very poor condition. 2 of 3 heater work
Check up on furnace, cleaned furnace, turned on gas, cycled furnace, inspected ductwork, burners are rusted, need to get price on new ones. Wants ventless heater gas line hooked up, will do that when we replace burners. Replaced burners, ran gas line to heater, Jeff will get the fittings we need and call Returned 11/6 and hooked up heater
AC Check Up, flushed drain, cleaned furnace, washed condenser, cleaned off pad, checked charge system cooling great
Broken spade terminal to capacitor. Warranty
Replaced condenser fan motor, fixed burnt element wire. Tested heat pump and defrost. Replaced 30A breaker with 60A, wired up another heater. Found defrost not kicking in, need a defrost sensor. Replaced defrost swt.