Great job. Very professional.
AC Check Up, flushed drain, cleaned furnace, washed condenser, cleaned off pad, checked charge system cooling great
Broken spade terminal to capacitor. Warranty
Replaced condenser fan motor, fixed burnt element wire. Tested heat pump and defrost. Replaced 30A breaker with 60A, wired up another heater. Found defrost not kicking in, need a defrost sensor. Replaced defrost swt.
Solenoid energized but not opening, need to order a new one Honeywell true ease HE300A1005 Replaced solenoid, cleaned drain line, humidifier pumping and draining correctly
Complaint: Gas furnace not heating Dead blower. Replaced blower Run checks okay.
2020 PCSA Heating Check Up Renew
Installed iWave air purifier Capacitor on blower motor was also weak and needed replaced.