My experience with Charlie's was seamless. They took care of everything. They gave me a great price and an excellent warranty and set up my financing for me with just a few questions over the phone. Their install team was fast and friendly and had me going in no time at all !
Fixed flue pipe for boiler, Pam only has a window unit, use ac cleaning to cover my repairs for today.
AC Maintenance Renewal Contactor on outdoor coil is looking worn. Would recommend replacement next AC check up. Everything else was clean and checked out well. System is operating normally at this time.
PCSA 2021 a/c maintenance free w/ install Changed filter customer provided all checks good
Quote for AC add on to existing evap. coil and furnace
Air Handler was frozen up last night. Filter is good. Replaced x13 motor under part warranty system is cooling
PCSA 2021 PREPAID AC MAINTENANCE completed pm unit ok. Flue coupler installed
Disconnect off to unit .put tie on
PCSA : PREPAID AC Check Up 2 Systems Selling House: Inspection report stated that the burner we replaced in Sept. is not lighting. Adjusted gas psi to York furnace, cleaned A/c unit in ok condition Freon is spot on. Ckd other system cleaned capacitor still has waarany
PCSA 2021 AC Check Up 2 system prepaid Downstairs system needed 8 lbs of R-410A. Customer wants leak search when possible. Downstairs system also has a fault in electric heater package. Half of the 3rd heat strip is drawing amperage at all times. Customer may want to replace next winter. Upstairs system will need new condensate pump during AC check up next year. Everything is operating normally. 4/12 Performed leak search. Found leak in liquid line service valve. Was able to work with valve and stop leak at this time. Future use of service valve may require replacement in the future. Everything else appears to be operating normally.
2021 PCSA a/c 2 system check up renewal Everything was clean and checked out well. Systems are operating normally at this time.
Free With Install AC Check Up Puron levels were a little off. Corrected levels and system is operating normally. Recommend double checking Puron levels during Fall Check up. Everything else was clean and checked out well. System is operating normally at this time. 2021 AC Check Up Free W. New Install & Done 4/8/21 2021 Heating Check Up Free W. New Install 2022 AC Check Up Renewal
No heat found board was putting out call for ac and heat. Disconnected the ac, furnace working. Ordered new board, signed up on service agreement. Set up appointment for Monday at 8 am. Need to bring a 2 inch pvc coupler Replaced board, cleaned furnace, installed nest thermostat, need to come out and replace 2 inch coupler on drain when itâ€™s not raining
Cleaned boiler, checked safeties, inspected flue vent. Part of it is rotting out, will address it this summer. Signed up on service agreement
Estimate For 95% Gas Furnace and AC unit