Very informative and friendly service,would definitely recommend them😊
AC Not Cooling Well. Topped off charge. Need more cleaning. Needs contactor
Quoted new 2 ton 16 SEER York heat pump system
Inside unit had a hot smell when turned on this season, found bad blower capacitor. Replaced capacitor, system is cooling. Would like a quote on a new system from Pete.
Unit runs constantly found bad capacitor, replaced, fan relay board is bad keeping heat on constantly. Customer will replace part himself, shut unit off at air handler
Meant to call Coulsons