Thanks for the fast service! We appreciate it!!
2021 PCSA a/c maintenance free w/ install Everything was clean and checked out well. System is operating normally at this time.
PCSA 2021 PREPAID AC MAINTENANCE Capacitor was getting weak on outdoor coil. Replaced capacitor. Contactor on outdoor coil may need replaced during a future check out. Everything else was clean and checked out well. System is operating normally at this time.
PCSA 2021 PREPAID AC MAINTENANCE Condenser fan capacitor was getting weak and needed replaced. Everything else was clean and checked out well. System is operating normally at this time.
PCSA 2021 AC Check Up Renewal 2 Systems We will have to bill customer he is in a meeting for work. All checks good replaced both filters Techs should be aware arco trips on thermal cutout when disconnect is pulled, works fine with disconnect in and board reset
Complaint unit freezing up Cause of the issue is stuck TXV. Replaced TXV and system is operating normally at this time. Everything was clean and checked out well.
RENEW 2020 PCSA Heating Check Up Found wire burnt up going to third heat strip. Left spare wire for replacement once customer runs new supply wire and disconnect to outside unit. Everything else was clean and operating normally at this time.
PCSA Fall 2020 Prepaid Heating Check Up Everything was clean and operating normally.
2020 Heating Check Up Renew & Scheduled11/9/20 2021 AC Check Up Included Fall PCSA check up, checked electric heat, cleaned cabinet, inspected all electrical, changed filter, tested heat pump, checked charge, checked electrical, could not test defrost, too warm out. System is heating
Maintenance on electric furnace, checked all elements, all heaters coming on, filter looks good, bring 2 next visit. Cleaned furnace everything operating well
2020 Heating Check Up Prepaid & Scheduled 11/9/20 Performed Fall PCSA 2 systems. Cleaned furnaces, changed filter upstairs, basement filter looks good. Cleaned all drains, pressure tubes and traps. Checked CO levels, set gas pressure, cleaned flame sensors, inspected all electrical both systems are heating well
PCSA Fall 2019 Heating Check Up Renewed & Done 12-9-2019 Spring 2020 AC Check Up Prepaid Everything was clean and checked out well.