We are very happy with the service we received. They responded immediately and gave us a very fair estimate for the work needed. It was scheduled and completed on time.
These guys are super responsive. Very cordial. They make sure to clean their boots when entering the house. They also explain everything at every step. Very professional. Good value.
The job was done and we had some additional problems. RA Nichols was only a phone call away. They responded quickly and to our satisfaction. It's nice to know they can be depended on not to forget their customers.
Paul was back on Saturday during a snow storm to fix another issue in our house. He came when he said he would. Did what he said he would. And even called to follow up to make sure everything was okay. He is a pleasure to work with, you have a true asset in Paul
Paul did an outstanding job on his first visit. He was thorough, new what he was doing, and talked us through the process. He absolutely exceeded every expectation as we were in uncharted territory and he was the map!
Took the time to deliver a rock-solid fix. Tom clearly knows his job and was a pleasure to work with.
Paul worked very hard along with his partner.......explained everything they were doing
Technician arrived and customer explained that both sinks had been backing up after extended use of water. Technician offered options and was given authorization to snake the line. Tech snaked out the line via pistol snake, working snake back-and-forth with multiple passes. Upon completion of snaking, sink traps were cleaned. Once Drain system was reassembled it was flushed with hot water numerous times flushing any debris left in the lines out. Then again cold water was flushed through lines ensuring that no leaks were present.
Cut open sheet rock ceiling where leak was - could not find a leak currently Ran tub with customer moving around in for multiple minutes Ran shower head for multiple minutes Let system sit pressurized to check for water line leaks - hot side should be replaced because of condition of piping - found no current leaks Could not find a current leak- believe there might have been an accidental spill or the shower caulking has gone bad
Install thermostat and complete annual heat inspection on Goodman furnace. Unit has some rust on heat exchanger but everything is in good working condition. No C.O readings in house. Unit does not have a filter which is causing blower motor to get blocked with dirt. Needs new filter asap. 20x24x1 or 20x24x4
installed 32 gallon well tank with new cross tee New pressure switch, pressure gauge, relief valve, boiler drain Installed new ball valve coming into home Installed township supplied water meter and meter reader outside Ran wire through garage and mounted on porch Tested no leaks all is complete and in working order
Replaced parts 2 year warranty on parts
Trip charge - left customer with options for cleanout replacement and garbage disposal replacement Trip charge to be deducted from work if customer moves forward with work
Duct cleaning *while on site customer mentioned interest on moving laundry down to the basement. Water supply from kitchen sink is in vicinity, however customer expressed having the desire to install a laundry sink next to the units. (See picture of basement 08/19/19)
Newer carrier unit had no a/c. Found bad capacitor and replaced. Unit is working at this time.
Filled unit with 2lbs refrigerant r410a
Bad condensation pump on unit causeing puddles on floor and water to not leave basement
Plumbing repair for residential customer for water leak detection. Customer had water lead and could not find it. Damp and moldy areas around the home drywall showing water damage. Diagnose pipe leak. Perform pressure and acoustic test. Shut off water valve, apply pipe repair clamp and replace damaged section of pipe.
Installed a new bathtub trip waist and drain for a residential customer.
Customer had a leaking kitchen faucet. We replaced it with a brand new faucet and dish soap dispenser.