Installed new float switch for sewage ejection System. Test it all. No leaks at this time functioned normally.
Installed customer supplied utility sink in garage.
Installed new hot ignitor on water heater. Also installed new check valve and ball valve. Found cross connections and isolated.
Main line clogged. Plumber will snake line through clean out at front of home and attempt to clear. Successful. Tested all. Good flow restored.
Rough in and top out plumbing for new bathroom.
Installed new under sink plumbing for the kitchen.
Installed new 50 gallon water heater
Replaced 14 year old water heater.
Pilot light on water heater won't remain lit.