Arrived at location on 7/13/21 - examined unit. Was able to get all stove pilots and burners to light. Pilots in worse shape than others. Showed maintenance team member how to properly light pilots. Upon leaving Tom Farrel showed up and stated the stove top is fine and that its the ovens that are acting up. Will order 2 garland 60inch oven thermocouples and return. Call Tom when coming. Returned on 7/28/21 - replaced thermocouple on both ovens both pilots lit and held main flame engages.
mounted garland salamander on American range at Bareilles restaurant mod GIR36 ser 2009100101718 fabricated secured as needed all okay
Examined Combi Oven unit, costumer wanted unit installed on line, after looking over unit found that it would have to be converted to LP gas, a power chord and install new gas line, advised maintenance that unit needs water line and drain installed before unit moved into place, will quote price. no guarantee unit will work, has many solenoids, gas and water. Note: quoting additional repairs, closing out this work order.
found Gas Fryer unit off, first unit on left serial number 48182811B customer advised that unit will work for few hours then read oil level low - cycled unit on, unit went thru nelted cycled and came up to set point no errors shut unit down and switch control to center vat to see if problem follows control or stays with fryer - called Vulcan, got voice mail, left message and cell number, waited 1/2 hour for return call, Mark called back and had me check drain switch error came up fill vat draining - adjusted switch and used wire ties on modules pin connectors to tighten assembly - unit may need s drain switch if problems comes back.
Left Fryer Unit not lighting, going into ignition failure, blower spinning, removed igniter, poor condition, tried to clean up. Unit lit, heated, cycled and cooked. Will order parts and return. 8-2-19 Replaced ignitor and tube and gaskets as needed, tested okay.
Went inside the walk in cooler and saw the seam the water was dripping out of. Had to go into the crawl space above the restaurant to access. It took awhile to get over to the hole so you could see the top of the walk in units. Found that there was about 15 feet of freezer line coiled on top of the walk in that had several inches of ice coming through it. The line was frozen solidly to the top of the unit. The ice was melting causing a big puddle of water that went over onto the walk in cooler and was leaking inside the unit. The best thing to do is to build a platform to crawl on so you do not have to worry about falling through the ceiling then running a new line set with 2 inch insulation covering the suction line. There was a ice build-up along the top of the freezer in a couple places too. All you can do with this is insulate, seal the gaps and hope for the best. Noted that the insulation on the lines has broken down over the years to this point. Try to adjust the fre
Examined Pitco fryer unit, pilot staying lit, main flame comes on sometimes, pulses and candles when cycling, needs new valve. 2-27-19 Disassembled and replaced the gas valve and thermopile. Reassembled and checked the. gas pressure and leak tested. Lit pilot and tested. All okay.