Henry and assistant are so helpful and knowledgeable
Henry and assistant were excellant. Worked all day. Really thoughtful on how to redo and create plumbing.
Pricing for trim at Campbell
Performed tankless water heater install as proposed New gas feed at this location with shutoff valve New hot and cold isolation valves with service ports New pvc venting through roof Ran temperature and pressure relief drainline and condensation drain to outside location All new plumbing tested no leaks Tested water heater, producing hot water No warranty on any existing plumbing
Performed rough in for kitchen sink Capped water feeds to claw foot tub Ran hot water to existing boiler location to tie in hot feed to lower bathroom/shower room Tested no leaks All rough in complete as quoted No warranty on any existing plumbing or plumbing fixtures
Installed laundry rough in Installed claw foot tub connections
Installed rough in plumbing for upstairs bathroom tub and double lav sink Cut existing sink drain and water capped inside wall Cut water piping and sewer piping to tie in new plumbing
Cut drywall and plywood to access wall Installed gas piping to new range location Capped gas feed on top floor (existing range location) Shut down water system installed new emergency shutoff valves near waterheater Installed code required earthquake straps on waterheater Cut out existing laundry drain piping installed new pvc drain piping tho pedestal sink open main floor bathroom
Took dimensions went through layout of existing and proposed location for new plumbing and fixtures
The gate valve on top of the hot water heater which isolates it was about 90% closed. When hot water was turned on to the fixtures that this tank supplies the pressure would drop because the valve was not fully open. Once I open the valve 100% there was no issues with the area is getting supplied hot water. I recommend spring of 2021 doing a hot water tank flush on all three tanks
I inspected the repair that was made by the care taker. I cut out the repair and made a new repair with Brass fittings. I removed the pvc water lines underneath the home and replaced it with new 3/4 inch pex. The existing water service was on the exterior of the home so I rerouted underneath the foundation. I replaced a failed hose bibb and shut off valve. I tested and everything is in great working condition at this time.