Jeremy and Crystal Blue Plumbing couldn’t be better. Jeremy took on a tricky problem with our tankless hot water heater. He was detailed, thorough, and kept after the problem until he solved it. Highly recommend the company and their Senior Tech Jeremy.
Taylor was friendly and knowledgeable. He found my problem quickly and fixed it to my satisfaction.
Excellent and kind
Not a problem, fast efficient and showed up on time. The only problems are that I was distracted by a neighbors dog in the yard and did not receive the info needed to cover the one year warranty on the pump. The second problem was that everyone, myself included, failed to open the drain from the holding tank that went to the pump. I realized there was a problem when the water pressure dropped on the front area irrigation area. I opened the valve and the system worked as it should.
Samuel came out and was very professional and informative.
Experienced , smart
Performed ac diagnostic, found smaller unit had a rat in it. See pictures, parts in range still, then tested system found smaller unit compressor drawing over max amps installed hard start kit and tested system This includes ac tune ups x2 Furnace tune up x2 Plumbing inspection
This would be after plumbing issue is fixed, we can cut back the 2 flex ducts to the metal main line in the wall, 4â€ duct and 7â€ duct. Need 2 splice collars, for other side. Then attach them correctly, sealing them and strapping them up into the bay for drywall.
Cut into existing water supply piping Replace water supply piping with upgraded copper Install up to 15 foot of water lines New water piping installed with flame three repairs for homesite Water piping for hot and cold water replaced Pressure test for leaks using house pressure Start up sequence included Remove approximately 10 foot of ventilation ducting Attach new ductwork to existing metal duct in wall We connect to flexible duct Office in order to replace wet damaged and unusable flexible ducting Cash price Total dissolved solids in water approximately 130 optimum total dissolved solids less than 75 Water hardness approximately six grains recommended approximately less than two grains
Performed leak search with plumber. Found pin hole leak in water line. Left quote for repairing ducts after plumbing has been repaired. 2 ducts need to be spliced into exsisting duct system and sealed then hung / strapped up into rafter bays for drywall.
Customer has a 11+ year old Rinnai tankless water heater that keeps tripping a 10 error code. Called Rinnai and they recomeded cleaning the exhaust fan, burner chamber, and all around cleaning the inside of the unit. After I went through the cleaning process the heater kept tripping the same error code, called Rinnai again. The tech had me use my manometer to check the gas coming from the manifold and he had me change the pressure on the gas valve inside the unit, tested and nw the unit seems to be working fine. The tech did mention the exhaust fan sounds weir and could be changed out, customer wants to test the unit for a bit and will contact us if we need to go that route. During this process I descaled the tankless on the other side of the home, and the customer will contact us next week to do the plumbing inspection as well as descale the unit in the garage.
Pulled tub and reset Customer satisfied with installation and additional adjustments will not be required
Technician Taylor arrived on scene to investigate reports of blockage with kitchen sink. Technician investigated further and found client had used rental snake to try to clear himself from both the laundry trap as well as the under sink clean out. Technician recommends another attempt with a secondary line drain machine. Client accepted. technician use secondary line drain machine to snake line approximately 55 ft. when technician removed snake and tested he found the drain to be operating properly. Technician use complementary video inspection follow-up to confirm blockage was cleared and flow had been restored. once that was confirmed technician cleaned work area of all trash and debris and answered all questions client had. Technician collected signatures and payment Secondary drain cleaning.
Customer called in to reschedule.
Technician Taylor arrived on scene to investigate reports of a leak with clients master tub. Technician found client to have three-hole tub completely encased in corner by tile and the master shower. Client loosened a set screw attempting to repair and the assembly fell into the dead space. The only way to access is to either cut tile or pull the tub. The tub appears to be a drop in with just a standard drain and overflow. Technician will provide proposals to attempt to repair.
Technician Taylor arrived to investigate reports of leak under sink. appliance believed it was coming from the P-trap upon further investigation technician found there was a pinhole leak in the pull-out sprayer hose. Technician recommends replacement of faucet. Client is selling home in six to eight months and want something new. Technician will supply proposals. Technician will install new single handle faucet with pull out head Technician shut off water to home and disconnected existing faucet. Technician installed new Kohler Sous industrial pull down kitchen faucet. Technician tested to ensure proper operation and installation. Technician cleaned work area of all trash and debris. Technician answered questions and collected signatures with payment.
- Cut into copper supply to add new shut off valve - Alter piping as needed to insert valve - Install 2 new angle stops - Test with building pressure
- Cable snake drain line to establish flow - Single pass to unstop and get flow - Customer flushed toilets and ran water to verify good flow - No Warranty NOTE - Drain line WILL stop up again, additional cleaning services recommend
Performed annual air conditioning maintenance. Cooler day. Gave unit a good bath, really needed it, coils starting to get dirty. Visual inspection of unit, electrical ok. Found corner of coil has been bent / damaged. Not sure what caused it most likely been that way since original install. Contactor ok. Dual capacitor 60-5 ok. Unit could be higher per code, 4 in above grade it might be 1in.so bottom of condenser pretty dirty.
Tee off of existing 1/14 black iron pipe and tie into poly piping. We will use the mega press and cut into the black iron pipe. We will put a tee with a coupling for the black iron and 90 up and over and 90 down into poly piping. This job is for the landscaper for propane line for the pool. There is no permit required for this job. Returned to complete work. I tee into gas line with mega press and tied into poly piping. Spray tested and pressure tested at 15psi for 15 min. No leaks or faults. Uploaded pictures , took payment from cyle bush from fig landscaping and emailed him the invoice
Upon arrival met with cyle Fig from the landscaping company. He would like us to tee into the existing 1 1/4 black pipe gas line and connect to existing poly piping that he has ran. No permit will be ran and I gave an estimate to complete the work using a mega press and mega press fittings. I took $80 deposit and order parts from Ferguson to be delivered Thursday morning. Job will be completed and landscaping company is paying for the work for the job. Emailed Cyle the invoice.