Michael is very professional and very thorough with our air conditioning issues.
Tom did a great job on fixing our water valve problem! He was very prompt, reasonable, professional, & friendly! I would definitely recommend & use him again!! He deserves 5 stars!!
Twice I've used Crystal Blue to do difficult plumbing jobs and twice the work was five star.
I have no opinion other than what I wrote in "Review."
as usual, CBP saved the day. They are my go to Plumber. Thanks again.
I called with a heating issue, and within a few hours I had no issues. They were timely, and very professional. Our technician, Jordan, was extremely knowledgeable, and explained the entire issue and process to me. Could not be more impressed with the service!
Crystal Blue Plumbings customer service and technicians are out of this world. I had a problem with a smell coming from one of my toilets and thought it may be related to the septic system or the wax ring. The plumber (Kevin) came out and found that the flange was set wrong and was cracked,he thoroughly explained the problem and began to work on the issue. I was then informed by my wife that we had a home warranty and unfortunately Crystal Blue was not a member of that warranty. Kevin and Crystal Blue were so understanding and supportive, reattached the toilet, cleaned up and were very professional. If I need any work done in the future I will call Crystal Blue and would recommend them to anyone in their area of service. I only wish they were attached to my home warranty and pray the company that I have to use is as professional and thorough.
Called with a problem in the bathrom The response was incredible. The plumber was so helpful and nice. Even gave us some exrra tips on different things related to fixing up a house .
Replace 40 gallon water heater with a Bradford white propane water supplyâ€™s need to be replaced, gas supply line . The base of the stand is rotted out and will need to be repaired as well thereâ€™s no t&p line to exterior wall access to the unit will require a second man to remove and help carry new one in to back yard so we do not damage new unit. Unit has shut down while I was up this estimate. We will need to replace shut off valve thereâ€™s no handle to it anymore replace unit everything is back to normal
Part has been ordered from Fergusonâ€™s part will be in August 9 late morning
Main line sewer backed up between cleanout and septic tank.#no this is the second time in two weeks will clear line and determine where the issue is. Cleared line found two issues on a belly starting in driveway off of the concrete porch and a second one at the tank as of now the line holds waste in both locations thereâ€™s no warranty on the work performed due to these conditions.
Repair guest and master bath toilets with new parts. Installed new kohler fill valves, new chemical resistant flappers and adjusted to manufacturer specifications. Tested both toilets many times for operation. Toilets are working like new.
Repair of ductless mini split system will consist of removing existing refrigerant from system. pressure testing system, checking for leaks using refrigerant sniff / detector and / or bubbles to determine where leaks exist at any of the flare fittings. some of the flare fittings may not be accessible due to the way units were installed.May have to cut into sheet rock to access fittings which could be additional charge depending on labor involved once all flare fittings are checked and repaired will perform a minimum of 24 hour pressure test to verify no other leaks exist. If pressure holds will put a vacuum on system to 550 Âµm or below. This will remove all noncondensibleâ€™s air moisture etc. out of system to allow system to perform at peak performance with just refrigerant in system. will charge system to manufacture specifications. system is estimated to have about 8 pounds of refrigerant will be additional charge if it goes over 8 pound. Will be a charge of $98 per flare fitti
Refrigerant test passed duct leakage airflow pass / fail
Loomis Main line backing up, run cable from clean out to septic tank Ran cable from clean out to septic tank 90 feet away, removed tank lid to ensure cable made it all the way to the tank. Pulled back sanitary product. Line appears to have a belly 2 feet from tank and concrete tank has crack. Septic tank may need to be replaced. Ran water from hose bib and had customer flush toilets. Line is clear.
Performed annual maintenance penryn. 3 yr gas package unit rheem roof. Checked blower ok. Checked dual capacitor ok. Gave unit a good bath watch for wasps nest removed a few small ones. Outside coils needed a good bath. Ac working well. Refrigerant good. Change filter more often.
Completed plumbing maintenance, water heater looks to be from 2006 it is a 50 gallon propane water heater located in a exterior closet, it has no gas leak, no expansion tank and does not have a water heater drain pan. Toilet in master bathroom looks to potentially be leaking around the base, lavatory sink has a foreign growth onthe wall and the base is warped, Guest bathroom also has damage underneath the lavatory sink and that toilet also has staining around the base. The kitchen cabinet also has staining in the base and starting to have a foreign growth. Homeowner had to leave could not get paperwork signed but will email a copy
Remove old equipment per EPA regulations and install American Standard 17 SEER 3 Ton heat pump down flow. Two stage with variable speed. Move inside closet electrical to other side of wall.. new electrical disconnect for condenser with new breaker in panel. Heat strips included. Basic thermostat included.
Main line backed up access clean out in back of building septic less then 60 feet out will run 300 machine to clear line and the video inspect.video inspection found no issues in line tested good .installed customer supplied garbage disposal.
Wax ring has failed needs to be replaced and re caulked to floor
Customer had water leaking out of Hosebibb connections for laundry, reccomend replacement.
AC not cooling Goodman split system diagnostic turned on system found condenser fan motor not running. tested electronics found bad capacitor. Repair replaced capacitor Completed diagnostic amp draws of the fan motor and compressor good, contactor good, refrigerant charge low with current temperatures and pressures indicate system needs to be recharged. A system charged to manufacture specifications will cool properly and more efficiently.
Penryn California heating AC service heating AC maintenance heating ac diagnostic AC not working no / low freon / refrigerant performed AC diagnostic upon arrival found unit calling for cooling outdoor fan running, blower motor running, compressor overheated not running. Shut unit down ran water over compressor to cool it off to test unit. Cooled compressor off retried to start compressor. compressor would not start thermal overload stuck inside of compressor due to overheating to many times.