Brandon was awesome! Fixed our a.c. in a timely manner, took time to check a few other things & listened to any questions & concerns. He didnt leave till he made sure things were all good.
Always have had great service..
My Interstate representative was very pleasant, professional, thorough and informative. He didn’t rush through the appointment, took time to answer all of my questions and made sure I understood his explanation of the service performed. Overall, it was a very positive and satisfying experience.
Jordan and the staff at Interstate Hrsting and Air are always wonderful to work with!
I recently had my HVAC maintenance checkup and once again the service provided was exceptional. My service rep, Isaac, took his time, answered my questions, offered suggestions, was highly professional, and cleaned up leaving things in as good or better shape than when he arrived. All in all, it was a very positive experience.
I am very happy with your service! The young man who came out was very professional, polite, and knowledgeable about his job and your service! Couldn’t be more happy!
Came out to call. Customer said system wasnâ€™t cooling down the home well enough, and the temp raises in the house during the heat of the day. I tested system to verify any issues with the refrigerant pressures. System had a 7 degree superheat. I then proceeded to check inside the home and found the air temp from duct work in the living area is 16 degrees hotter than any other duct work in the home. I checked upstairs and found the ductwork running to the living room coming apart. The duct work overall is in bad shape and should be replaced. I gave customer options on replacing just ductwork or ductwork with AC and Coil, seeing that the coil is going to have to be taken out to get the new plenum in. Customer will discuss options with husband and let me know.
Performed preventative maintenance on AC system. Inspected blower assembly, electrical components, wiring, evaporator coil, drain, and overall condition of equipment. Changed batteries in outdoor sensor, and checked filters. Checked and tested thermostat operation, capacitor, contactor, compressor, fan motor, amps, temperatures and pressures of condenser unit. System is cooling properly within manufactured specifications at this time.
I came out for a blue plan AC maintenance. I washed the filters and condenser coil. I checked the blower, evap coil, condensate pump, capacitors, contactor and all wiring. I cycled the ac and checked all temps, amps and charge. All working well.
Arrived to no cool service call performed system evaluation on older York package unit. Found blower motor not spinning at correct rpm. Spoke to customer. Customer chose to replace motor. I installed new blower motor and capacitor. Amp draw in range. Cycled unit multiple times. 1yr motor warranty. System is cooling at this time.
I came out for a silver ac maintenance. I washed the ac coil. I changed the filter, they supplied. I checked the blower, drain, evap coil, capacitors, start kit and all wiring. I cycled the ac, from the thermostat, and checked all temps, amps, and charge. All working well.
Perform blue shield protection plan air conditioner maintenance. Changed filters. Test capacitor and motor amp draw. Test compressor amp draw. Test refrigerant levels they are in range for current temperatures. Evaporator coil is clean. All amp draw and temperature difference in range. Washed condenser. Furnace surge protector is in working order. Suggest surge protector to air conditioner. Surge protector for air conditioner is 136.00 System is cooling at this time.
Remove existing coil and install new 2.5 ton coil with txt, new drain line and float switch. Set new ac 14 seer 410a unit with 1/2 whip and 30 amp disconnect on pump ups. Coil has 10 year warranty and condenser will have 10 year warranty
Serviced a Goodman furnace and replaced a capacitor on a blower motor
Preventative Maintenance Service on Goodman Residential Furnace. Blower capacitor needed replacement
Perform silver club furnace maintenance
Preformed fall maintenance on 2 systems
Carrier furnace fall heat tune up
Furnace tune up scheduled on maintenance plan.
Preventative Maintenance Service on 8 year old Goodman AC. AC coil cleaning. Hard start kit recommendation.
Repair the Goodman air conditioner