Will always use Interstate H&A. They don't rip you off, Like the other ones...
The fan on my A/C unit quit blowing on the hottest day of the year. The whole staff at Interstate Heating and Air Conditioning were polite and knowledgeable. Jorden had my A/C up and running quickly. He even washed out the outside unit and gave me tips on keeping it clean.
Had my ac unit stop working. They were able to get me in for an appointment quickly. The service tech came, was very polite, and informative explaining the issues. He provided exceptional customer care. The office personnel as well whim took my call was also very polite and informative.
Isaac came out and did another fantastic job. This guy is happy in his job and it shows! Be sure and save a date in the fall with Isaac for my next heating maintenance service. Thanks!
I would recommend this company to family and friends, Brandon was very professional, friendly and on time if you ever need service call interstate heat and air first.
Adam took his time servicing the units and explaining what he found that needed attention, well above average.
Preventative Maintenance Service on Carrier Furnace
I serviced two systems for winter operation. Replace a hot surge ignition on one system
Preventative Maintenance Service on 2 year old Carrier Residential Package Unit
Replaced a control board on a Goodman furnace
American standard AC not cooling. Dual capacitor swollen and unit undercharged. Install new capacitor and add r22 refrigerant
Ruud system not cooling. Blower motor locked up. Install universal blower motor and run capacitor
Coil and condenser change out carrier equipment. AC is on, home not cooling.
Ruud AC not cooling properly. Cleaned evaporator coil and adjust refrigerant charge.
Perform a tuneup on the Amana air conditioner
Inspect ductwork in a crawl space under a house.
Found a faulty heat exchanger bid new system
Replace contactor switch and test capacitor, motor and compressor amp draw, refrigerant levels are in range to 2008 goodman air conditioner
Lennox AC not cooling. Dual capacitor swollen and bad. Install new dual run capacitor
Add refrigerant to the rheem air conditioner
Replace the control board in the Lennox gas furnace