Prices are not affordable!
Isaac is very knowledgeable and explains things in a manner where everyone can understand!
Another good job.
Tyler did a great job servicing our AC! Thank you!!
Couldn't have ask for better service.
Kianoosh and Jerimiah did a great job on spraying insulation into my attic. I'm very pleased.
Kianoosh was great. He explained everything in detail. Work was done in manner described and Kianoosh cleaned up everything before he left.
Great service, provides enough detail and very timely
Excellent Service, Average price, will recommend to friends.
Jason was very polite and professional. Great asset to your company.
Came in for a quote, was very informative, very friendly 👍
The experience was great and was courteous and professional
Silver club heating maintenance. Joe(JC)Ritchal. 11/30/2022 Performed full system evaluation and safety inspection. Checked blower motor, blower wheel, inducer motor, hot surface igniter, gas valve, gas pressure, gas line, flue, burners, heat exchanger, performed carbon monoxide test, cleaned flame sensor, and checked flame sensor. System is operating correctly at this time.
Arrived for previous customer no heat, spoke with tenants about the issue. System just stops working. Inspected furnace found gas valve not coming on with the system. Cycled system several times gas valve kicks on now. Cycled the system several times to test gas valve. Everything seems to be working. Will have to call in the AM for pricing pausing call for now.
Performed preventative maintenance on 80% gas furnace. Spoke with customer about how the new ac was operating for them, and they are pleased with it. Checked inducer motor, pressure switch, hoses, electrical components, blower, blower capacitor, and heat exchanger. Bottom of heat exchanger cells have hot spots. Checked gas pressure, carbon monoxide readings, temperatures, gas pressures and amp draws. System is working well at this time. Customer was interested in duct cleaning. Went over levels of duct cleaning and let customer know that she should be receiving a free one next fall, but to check with the office.
I arrived to discuss a duct cleaning and possible plenum replacement. I inspected the duct work and found 90% of it to be metal duct work. The bathrooms are flex duct to the metal trunk lines. The plenum is in good condition on the outside and sealed properly. We agreed to leave the plenum and preform a duct cleaning on the duct system. We will also install a whole house air purification system in the supply plenum above the evaporator coil. We will lay drop cloths in the areas we will be working. We discussed a better filter system but the homeowner will start to replace the filters monthly to help catch the duct and dirt. I explained that the systems do not produce the dirt but it carries the debris in the air that it moves. A duct cleaning will remove the debris from the ducts and the air purification system will help keep the air clean and oder free. Performed a duct cleaning for customer. Property was about 1,000 sq ft with 8 vents in total. (7 supplies and 1 return). Before cle
Arrived at the home to provide tune up. Upon arrival customer said to her knowledge system was working properly. Talked to customer about the things I will be taking a look at today. While doing tune up I discovered system was a 26 year old Rheem system. System has a crack in the induce draft motor assembly, rust buildup in heat exchanger, with the crack in the draft motor assembly and rust build up in the heat exchanger system is putting off carbon monoxide into attic which is a health hazard. single wall flue elbow going to double wall pipe thru the roof. Also found system with dirty blower wheel with dirty blower wheel the system is unable to move adequate air thru system.(unable to pull to clean due to truss blocking it). Condenser also has condenser fan motor and shield from a different unit installed on it. Went over everything with customer and made her aware of the concerns we had with the system. Also gave pricing and options with the customer. I had customer sign a heat e
Sam J 10/21/22 - arrived to White club member for fall tune up. Spoke with customer and they explained they had ran heater earlier in the week and no issues at this time. Fired furnace from thermostat and checked blower motor and inducer motor amps. Cleaned furnace interior with vacuum and wiped down exterior. Cycled system off then cleaned flame sensor and checked heat exchanger. House has (5) 12X12X1 & (1) 14X24X1 filters which we are going to return at a later date to replace due to not having all (5) smaller filters. Joe(JC)Ritchal 10/27/22. Dropped of 5 12x12 filters.
26OCT2022 Jason B Arrived for fall tune up, spoke with Loretta about the systems performance. Pet the cat. Inspected coil, blower cabinet, motor, and all electrical components at the furnace. Pulled blower motor and inspected heat exchanger. Clean flame sensor. Cycled system into heating ran system for ~15 min. Performed CO detection. 0ppm CO present home is equipped with CO detectors. Spoke with Loretta about duct cleaning and findings. System is safe and ready for the heating season. Changed customer provided 16x25 filter
I arrived for a new customer no cool call. I first spoke with the homeowner/tenant and found that the indoor system will run but the outdoor system won’t. They also mentioned that they can hear a dripping noise coming from the indoor system at times. I found out that this is a family/rental property and all extensive repairs will have to be approved by their Mother. I inspected the system and found the contactor to be the main reason the system would not run. The contacts are pitted, burnt and bad shape. I cycled the system on and found the system to come on intermittently but it is running at this time. I recommended to replace the contactor at this time. Once the system was up and running I checked the systems refrigerant charge and found it to be running at a 34 deg superheat and the system calls for 18 deg. This system is low on R22 at this time. I made this aware and that we can preform a leak search to find the leaking component and see what expenses it would take to correct this
Performed preventative maintenance on furnace. Customer wanted home tested for carbon monoxide. Told him that it’s included with the service that we provide. I inspected the blower assembly, motor, capacitor, other electrical components, heat exchanger, burners, flame sensor, ignitor, gas valve, inducer motor and overall condition of equipment. I didn’t locate any compromises in the heat exchanger at this time. Just hot spots on certain areas. Blower wheel and housing were dirty, so I recommended that I clean it for him. Discussed pricing and customer approved it. I pulled the blower assembly, and disassembled it. Cleaned it thoroughly with the water hose. Put it all back together, showed customer what it looked like after and re-installed into the system. Cleaned flame sensor and dust off the burners and components. Checked thermostat operation, wiring, amps, temperatures and gas pressure. Did a carbon monoxide test and system had 0 ppm. Unit is getting older and will need to be repla
Came out to call for a system not heating or cooling properly. Checked system over and found a heavily clogged filter. Filter hadn’t been changed since January of this year and was creating a major restriction in how the system was operating. I replaced the filter and tested system to verify the unit was working. AC and heat worked without issue. Tenant needs to be more consistent in changing the filter every 2-3 months.
I arrived for a new customer new home no cool. I spoke with the homeowner and found that the system has not had a filter in it and the system is freezing up. I inspected the outdoor system and found the system refrigerant charge to be low. I then inspected the indoor furnace and evaporator coil and found the filter to be completely stopped up and the blower wheel and evaporator coil to be clean. The filter had not been replaced properly within two years. I removed the filter and installed a new filter that was in the furnace closet. The system is installed behind the dryer. You have to move the dryer every time the filter needs to be replaced. I then checked the systems refrigerant charge and found it to fall within normal range. I recommended for me to cut in new filter grills and clean and seal the return cavity properly so the dryer will not have to be removed every time the filter needs to be replaced. The homeowner is going to check and see if he can do the job and will let us kno
Jesse 9/20/22 arrived at job found unit is frozen up nothing I can do until thawed unplugged disconnect so it can’t run left the blower motor running so it will help thaw coil. Jesse 9/21/22 arrived at job found unit low on r-22 two lbs added and then checked fan and filter customer changed filter and will clean her own condenser that I recommended her to do the condenser is not blocked with Cotten wood but there is dirt on it she says she cleans with water hose regular the system is working at this time.
18SEP2022 Jason B Arrived for new customer no cool. Spoke with Faith about the issue. Thermostat wire came apart at the AC. Cycled system at the thermostat. Inspected coil and furnace. Inspected Ac. Manually cycled system at AC. Reconnect thermostat wire with wire caps, and zip tie wires to lineset. Found liquid line pinched 95% shut at AC. attached is estimate for repairs.
I arrived for a warranty no cool call. I inspected the system that I recently put a capacitor in and found that the condenser fan motor is pulling 0.25 amps over its amp limit. I made this aware to the homeowner and we discussed replacing the condenser fan motor or replacing the system. The homeowner wants to wait until Tuesday to talk to his bank to see if he can replace the system. I gave the homeowner a 30 day money back guarantee on the repairs that we have already done if we replace the system vs keep making repairs.
Blue shield club maintenance. Joe(JC)Ritchal. 09/02/22. Perform full system evaluation and safety inspection on an outdoor side discharge package unit. Checked refrigerant charge, checked sub cooling, checked compressor and fan motor amp draw‘s, checked capacitor, checked lower motor, blower wheel, blower motor capacitor, washed condenser coil and changed filter. System is operating correctly at this time.