Always a pleasure to do business with interstate heating and air. Great customer satisfaction always.
Absolutely GREAT! Your employee is very good and very informative when I had questions.
Chris did a great job explaining everything to me.
As usual, Interstate Heating sent a highly qualified technician for the biannual check. Chris did a super job!
And a military discount
Chris, with Interstate Heating & AC take great care of my 3 units. Thorough job. Just right!
All right 17 June for an air conditioning preventative maintenance on inspection of the condenser found that the capacitor was low customer authorized replacement with a turbo capacitor checked charge on unit had 14Â° superheat with a 8Â° sub cooling checked evaporator checked drain line checked blower everything else was within tolerance. Customer changes their own filters.
Arrived 17june for ac pm inspected evaporator and blower checked blower capacitor. Checked condenser cap and contactor all was within tolerance. Checked charge on system 25 super heat and 13 sub cool washed condenser
Rive 17 June to conduct to a C PMs found that the downstairs unit was 2 pounds low on 410 a customer authorize top off does not want to leak search at this time I may consider in the future clean both both condensers customers change there own filters checked contactors capacitors in both units checked blower evaporator both units everythingâ€˜s within tolerance at this time.
Arrived 16june for ac pm found that condenser had a bad capacitor customer gave permission for replacement. Checked charge it had 10 super heat and 8 of sub cooling. Checked contactor and evaporator and blower. Ensured drain was flowing cleaned condenser customer changes their own filters.
Arrived on 16 June for eight air conditioning no cool. Customer already knows they have a small leak in the unit did not want me to do anything to the unit besides top off the 410
Row 16 June for a blue shield air conditioning preventative maintenance found that system of the Pound low on 410 a customer authorized to top off check drain evaporator blower contactors and capacitors everything was within tolerance wash condenser changed filters.
2 system white shield plan AC tune ups. Spoke with customer and north system is not cooling at this time. After inspecting units in attic and at condensers, found the 24v thermostat wire on north side to be deteriorated and shorting out, also found capacitor on fan side nearly depleted and on compressor side completely depleted. Went over options with customer and decided to put in hard start kits on both units, install new capacitor and fix 24 v wiring in north unit. Washed condensers thoroughly, changed filters included with plans, checked furnace blowers, evaporators, drains and flue. Checked amps on blowers. Checked, changed capacitor in condenser. Cleaned access ports, checked refrigerant charge and electrical. Both systems working great at this time. Did not have hard start kits in stock at this time, will return ASAP to install both of them. Adjusted discount to reflect 15% off for White shield plan Returned 6/15/21 and installed both hard start kits. Tested and verified proper
Arrived on 15 June for a blue shields air conditioning service panel inspection of condenser capacitor found the condenser capacitor was working but was below tolerance customer authorized change checked blower capacitor that one was within tolerance flush drain with Clearwater checked refrigerant levels had a 20Â° superheat on a fixed office system with a 13Â° sub cooling
14JUN2021 Jason B arrived for failed inspection. Reinsulated the lineset. Add insulation in between the clamp and liquid line. Cut underlay away from B vent.
Helped customer set up Nest thermostat, checked and changed customer supplied filters
Arrived on 14 June for an air conditioning no cool found that the system was a little low on charge customer authorized top off and also purchased red club membership so I added 2 pounds customer got 1 pound for free on the red shield plan what did discuss with spouse about doing a leak search on system.
Arrived 14th of June to conducted air conditioning preventative maintenance inspected blower evaporator checked capacitor on blower capacitor was within tolerance checked contactor capacitor and hard start kit on condenser always within tolerance had one amp on condenser fan motor and 14 A on compressor this is a fixed orifice metering system had 20Â° Superheat and 7Â° of sub cooling system does not have a float switch installed customer is selling house and will let new customers deal with this problem. customer supplied filter changed customers filter.
Came out to call for a system not cooling properly. Customer stated we were out yesterday to do a repair on the system and it worked until this morning. Then it stopped working again. I checked system over and found it freezing up due to the blower motor not operating. I checked blower motor and blower capacitor and found the blower capacitor to be bad. Made homeowner aware of the repair needed and also recommended more attic ventilation to keep heat levels manageable in the attic during the summer. It was easily over 140 and they unit was already under stress to cool the home back down after fixing it the first time. Apologized to customer for us not doing a quick check over the rest of the system, and discounted todayâ€™s repair because of having to come back out. Replaced the blower capacitor and cycled system on to check operation. Checked amps, temperatures and pressures of condenser, as well as the amps on the blower motor. Blower amps are within range at this time. Recommended c
Arrived 12th of June for a no cool found ice on evaporator indicate a leak customer did not want to do a leak check system also while running and checking the charge on system it had a 70Â° superheat this is a fixed orifice system it at 33 psi G on the suction side -17Â° saturation suction side defrost system and is currently running.chris
Arrived 10th of June for a noise customer thought it was short cycling it was not short short cycling she found out from a neighbor that they were working on the substation check charge found it it was a pound low on our 22 customer authorized top off system is working as should at this moment.