On time. Quickly diagnosed and repaired problem and charged at a very competitive price.
Tech was very courteous and professional. He performed the work expeditiously and made a couple of useful recommendations. Really excellent service!
Jordan came out and really spent time ensuring the unit was operating efficiently. Gave me advice on what was needed
Very efficient and considerate
Our air conditioner was not working. We called and they came out the very same day, even earlier than they said. Our units are old, but they got it up and running great again. They are always friendly and do all they can to make sure you are happy with their service. Thank you!
As always Isaac did a great job replacing the compressor in the pouring rain.
From the scheduling to the diagnosis to the quote, repair and installation, Brandon and Jason did an awesome job installing our new HVAC unit. Professional, curious, knowledgeable and honest. We have been long time customers and will continue to rely on Interstate for all our heating and cooling service!
What a great experience. I called Interstate at 4pm on a Friday. By 5:30, my AC was running great, I had been educated on how the system works, what mine needed, the cost of the parts, all discounts available and also informed of a maintenance package that I didn’t know existed. Had I had scheduled maintenance, my issue probably wouldn’t have occurred to begin with. Patrick was extremely courteous, communicative and fast. Really glad I called Interstate.
Replace 1st year warranty evaporator coil. Pressure check lineset. Pull vacuum add r410arefrigerant
AC tune up on Carrier 6 year old system. Floor duct inspection to repair collapsed in ground ductwork.
Carrier AC tune-up on 6 year old air conditioning system. Collapsed floor duct quote to repair and reconnect duct line.
Replaced thermostat on a carrier system.
Serviced a carrier system for summer. Replace contactor. Replace capacitor. Replace hard start kit. Wash out air conditioner.
Serviced three Air conditioner for summer maintenance. Wash out condenser. Replace capacitor.
AC maintenance on a 1997 Lennox system.
AC repair, found 2000 Ruud system to be low on refrigerant. Customer just wanted to add refrigerant, added 3lbs of R22
Check minisplit lineset and pull vacuum. Cycle and check operation.
Test compressor amp draw, capacitor and motor amp draw, test refrigerant levels to Lennox air conditioner
Air duct cleaning for floor vents that are struggling to cool room.
AC maintenance on 2, 2012 Amana systems. Added pan treatments to prevent clogged drain lines.
Serviced and clean outdoor condenser. Clean drain. Add pan treatment. Lennox ac system.
Changed filters, test capacitor and motor amp draw, test compressor amp draw, wash condensers and check refrigerant levels to both carrier air conditioner
Carrier 2017 16 SEER Air Conditioner maintenance plan.