Came as soon as available and the usual great service. Thanks Brandon!
30OCT2023 Jason Brown Arrived for new customer no heat, spoke with Michael about the systems performance. It’s never worked well, but now it doesn’t work at all. Inspected Airhandler. Found 120 to ground but only 10v instead of 240v. Inspected breaker panel. Found water draining down the panel, and the 60a 2 pole Eaton breaker corroded and split. Spoke with homeowner about my findings, he will contact a electrician. Left panel off, power off, and panel screws next to panel. System is not working at this time. I do not recommend restoring power to the home until an electrician has looked at it.
I arrived for a friend’s and family no cool call. I inspected the system and found it to be heat or cool only thermostat but you had to select the heat or cool in the furnace. I found the selector fan relay to not be making electrical connection. I replaced the relay and found the system to come on and run.
I arrived to bid a 3 ton system in a 4500 sq ft building and two mini splits in the dressing rooms. I inspected the building with the building manager and he showed me where and what he wanted. I explained that the 3 ton system will not cool the building as needed. He understood and only wants the bathrooms and the dressing rooms conditioned. We will be installing a 3 ton system in the attic space and will be dropping a 10” duct to the bathrooms and kitchen area. The rest of the air will be dumped into the large 4500 sq ft area with a manual damper that they can shut off and just condition those rooms. I will be showing the installation team what will be done due to the custom demands of the building manager.
Fake call no opportunity no sail.
I arrived for a previous customer no cool call. I inspected the system and found the modulating blower motor to be running backwards. I will track down a motor and the cost tomorrow and contact the customer with price and availability. replaced motor- customer is out of town, bill customer
Unit frozen. Need to let thaw out. 7-11-2022– returned and removed top from unit and found indoor coil plugged and drain pan full of debris. Brushed coil and cleaned with rinse less coil cleaner, removed debris from drain pan. Checked operation. All amps and pressures are good. Have a 20 degrees air temperature drop. System is operating normally.
09JUL2022 Jason B Arrived for silver club no cool. Spoke with homeowner about the issue. Condenser fan is not spinning. Cycled system at the thermostat. Checked filter and indoor equipment. Inspected AC. Found dual run cap out. With homeowner permission I replaced the capacitor and cycled the system. Checked all amps and pressures, washed condenser coil. Replaced existing filter with complimentary filter offf truck. System is cooling properly. Please give it some time to cool off before it starts feeling normal.
Came out to call, tenant stated that the heater was running constantly and not shutting off. We were out recently to fix another issue on the system. I checked the system over and found the heating elements activated and the thermostat not calling for it. I found the double stack sequencer had failed and was causing the heater and fan to run constantly. I replaced the sequencer and double checked system operation. Heater is no longer running constantly, and system is operating properly.
26APR2022 Jason B Arrived for a not cooling well, spoke with Tenant about systems performance. Itâ€™s blowing air but itâ€™s just not cooling. Inspected system found coil freezing and system low on refrigerant. Spoke with homeowner about age of system and probable leak. We decided to get tenants cooling today. Weighed in 3lbs of r22. System is running properly at this time.
Performed silver club heater maintenance. Filter was clogged and causing limit switches on elements to trip. Replace filter. Test capacitor and motor amp draw. Amp draw in range. Test sequencers, relays in limits. All are in working order. Amp draw to 1 side is slightly elevated but in working order. Breaker could be in a little better condition. Spoke to customer about it. Customer will replace breaker if needed. Unit is putting out 120f heat. Heater is working properly at this time.
Arrived to service call we replaced ductwork and plenum recently. Customer was due to have free air flow adjustment. Performed adjustments to area that customer had concerns. The adjusted areas where kitchen and living area. Opened living area all the way and dining halfway. Customer stated airflow was good. Also showed customer how to adjust airflow for any adjustment needed in future. Airflow in all areas is strong and system is heating well at this time. No charges to customer
Replace ductwork with correct sized ducts and metal plenum
Performed duct inspection gave estimate to replace ducts with correct sized duct for 4 ton system complete with metal plenum. Will apply todayâ€™s balance towards repairs if customer chooses to replace ducts.
Arrived to no cool service call performed system evaluation. Found system frozen up solid. Unthawed unit. Found system low on r22 refrigerant. Spoke to customer at this time customer chose to add refrigerant to system. With customer approval I added 1lb 13 oz to system. System is cooling at this time. System is starting to show signs of age if becomes low on refrigerant in near future suggest leak repair or consider system replacement due to age and condition. System is cooling at this time.
I arrived for a non member cooling to much call. I first inspected the indoor furnace and found the systems to be running with the thermostat to be calling for cooling. I removed the doors to the furnace and the door switch turned the system off. I turned the thermostat to the off position and supplied powerful back to the furniture. I cycled the system four times from the thermostat and found the system to shut off and turn on when told to. I could not inspect the evaporator coil due to the evaporator box is installed in a plywood and metal box around the evaporator coil box. I recommend to have the system repaired before any further issue present itâ€™s self in the future this system is 26 years old. I inspected the condenser and found the systems to be running and the high side schrader core to be broken and was leaking refegerant once I remove the cap. I tried to remove and replaced the schrader core but it will not remove. I tightened the cap back down on the high side king valve