Brenda in the office made it very quick and easy to set up my services. She was very Informative and let me know all the details. The technician Luis was great and took care of the first scheduled maintenance we had set up. He answered all my questions and is very skilled in what he does.
Response from Mega Care Solutions:
Rey we will pass along your kind review to both Brenda and Luis. Thank you for trusting us to care for your HVAC needs.
Luis was great to work with! He is very polite, very respectful, and very helpful!! Thanks Luis!
Portable unit, we replaced a thermostat and filter was really dirty hasn’t been changed in 2 years causing the unit to freeze up Kitchen unit, does not have freon and compressor is grounded contacted Toby to work on estimate contact Tracy Owen (principal) 432-254-0561 Towen@stanns.us
Float switch was not allowing the outdoor unit to come on we need to get back out there to replace did not have any on the van. Also replaced a contactor that was starting to burn up. Everything else looks good to go
Completed a tune-up and left the carbon monoxide detector with our awesome customer. Our thorough service ensures optimal HVAC performance and safety. Providing peace of mind, the detector enhances home safety, detecting potentially harmful gas leaks. Another successful maintenance check ensures comfort and security for our valued customers.
Went out to a scheduled furnace replacement at a customer's home. Their old system was carefully removed and the new unit was meticulously installed. The heating system is operating as it should for the customer.
Furnace repair for a residential customer. We found the issue after letting the furnace cool down. The flame sensor was not giving an efficient current to the system. The flame sensor was replaced and the issue is now resolved for the customer.
Ecm blower motor needs to be ordered, Johnstone didn’t have in stock (communicating system Lennox) air handler model #cbx40uhv060230602 Serial#1612d05006 1hp, 120/240v
The unit checks out to be good to go. Went through a check and did not find anything I ran the unit to 80 kicking it on and off and everything good to go.
The unit had a transformer connected to a timer that was out replaced the tram and everything kicked on and good to go
HVAC repair for a customer in Midland. Upon inspection, found that the pressure switch was bad. Replaced the switch and now everything looks good to go.
Everything checks out good
Unit had a dirty flame sensor at time of visit
Installed flood safety switches for a residential property. Focused on safeguarding the HVAC system against potential water damage. Ensured proper placement and functionality of the switches, providing the homeowners with an added layer of protection during floods.
Performed routine HVAC maintenance on a residential system, checking and cleaning the air filters, condenser coils, and evaporator coils. Inspected the thermostat settings and ensured proper refrigerant levels for optimal cooling efficiency. Lubricated moving parts to reduce friction and conducted a thorough system test to confirm smooth operation and identify potential issues before they escalate.
Heat pump repair: Diagnosed a faulty reversing valve and promptly replaced it to restore the heat pump's ability to efficiently switch between heating and cooling modes. Tested the entire system to ensure proper functionality and optimal heating performance for the residence.
Maintenance complete everything good to go.