Our technician Heinz B. knew exactly what he was doing, was honest about the repairs and extremely quick. Would definitely trust him to come back again if needed. Excellent work!
This is the second time John has been to our home. He is extremely friendly and engaging and And keeps us informed from start to finish what the problem is and what possible solutions are so we can make an informed decision
Yamil was a great. Very professional and friendly
it was a very helpful service. I was assured my boiler is fine.
We use Clearview Services for all our work. They are excellent. Heinz explained everything, made suggestions. As always Bravo Clearview.
Hi 👋. Only thing I can say is: John is the best
Response from ClearView Services:
Thanks for your feedback, Moses! We are disappointed that you feel our prices are higher than you expected. This is exactly why we offer the upfront pricing so if you choose to not use us, we can part as friends. Our regular customers prefer this peace of mind when trusting their repairs to a service company. We hope you were able to find a provider to meet your needs.
Today I came to Jitkaâ€™s Bearspaw home because there is once again, no hot water. Upon inspection I found the same error saying ignition retries. This means the boiler failed to ignite. The control board, ignition module, igniter, gas valve and gas valve cable have all been replaced as per tech support. The system initializes, spark igniter sparks, gas flows and no ignition. I once again took the boiler apart and checked the seals, refractory plates, burner and heat exchanger. The system is in good condition but will not fire. I triple checked the setting for air gas mix and set it according to manufacturers specifications. After many attempts I was able to get the boiler fired up and running, Jitka now has hot water however I do not know for how long. I am scheduled to return Monday with the combustion analyzer to check that the air gas mixture is correct. The manufacturer specifies the air opening for this model boiler be 9 turns open. I was only able to get it to fire consistently
Today I came to Kens Varsity ho e because he is concerned about his sewer line. 15-20 years ago he had to have the line augured due to root intrusions. He has noticed several drains that are getting slow and would like the line inspected. Upon camera inspection I found the line in poor condition. The internal cast iron piping system has advanced â€œChannellingâ€ and is developing holes in the bottom of the pipe. There is a large root intrusion 3-5 feet from the cleanout. The exterior concrete asbestos piping system is also in very poor condition with smaller root intrusions and large pipe misalignments.Return today Friday 18/21 to complete the work needed,Jb to do remove concrete sections in basement room to have access to the main drain line ,After Remove concrete and excavated we fund the cast iron Y was broken and built up with mud and debris,after removing the damage cast iron,we run the camera from the main stack clean out access and view the conditions of the main drain from the
Client called to have second floor shower trim replace and to have a look at in floor heating is not working. Tech went out qouted to replace second floor shower trim client supplied. And tech quoted to replace infloor heating pump. Client approved work. Tech drain system and replace the shower trim and the cartridge the the client supplied. Tech informed client the tub spout is not the right one for what he has unless he would line a new shower control. Client will get the right tub spout and do it him self. Tech removed old walco pump and installed new Grundfos pump tech tested for leaks and functionality infloor heating working well. Client is happy 10/10
Today I came to Jenniferâ€™s new Quarry park home because the Ac system has not been working. Upon visual inspection I found the starter has failed. This must be replaced before further diagnostics can be done. I have installed the new starter / capacitor and tested. The unit is working now however it is very low on refrigerant and needs to be recharged. I have recharged the system and it is working well now.
Today we came to the Williams residence in beautiful area of macewan. Isolate drain and remove existing 50 gallon HWT and associated venting, gas and water piping. Install new Navian tankless unit with furthest fixture bypass. Install and test new gas and water lines, and associated vent and air intake piping for the products of combustion. Run new condensate drain line. Test unit no leaks present. Mr Williams was very happy with the service today and would rate us a 10 out of 10.
Tech return today June 18 2021 - Tech Heinz Tech returned today to install new circulation pump for domestic hot water. Tech drained system and install new pump. Tech supported new pump and installed temperature sensor, tech tested pump for leaks and functionality. Pump appears to be working well. Tech left Manuel with the combination boiler. As tech was cleaning up tech noticed the sump pit was getting very full and the sump pump was not coming on. Tech removed pump and reset the pump. Still the pump would not come on. Tech used multimeter to tested the electrical plug in for power. 120 VAC is confirmed. The pump has died and will need to be replace. Tech informed client and quoted to replace pump. Client approved. Tech installed new pump and reconnected drainage. Pump working well, pump drained sump pit within seconds. 1 year warranty on recirculating pump 2 year warranty on sump pump System is working well client is happy 10/10 Tech returned today June 7 2021 -Heinz Tech returne
Today I came to Jamieâ€™s Bayview home to perform the annual Ac system inspection. Upon Ac inspection and service I tested temperature drop, relative humidity, air flow, motor and fan, compressor, capacitor, contactor, evaporator and condensing coils, and refrigerant levels. The system is 14 years old and uses obsolete r22 refrigerant. The refrigerant levels are low and the torque booster / capacitor is rusting on the top. The unit is not equipped with a compressor saver. I have explained my findings to Jamie. He does not wish to put any money into the Ac at this time and will replace it when it finally dies. He is happy with todayâ€™s service.
Today I came to Marioâ€™s Acadia home because the sewer recently backed up into the basement. This has happened before however not as severely. Upon camera inspection I found the internal cast iron piping system is deteriorating and depositing cast iron in large amounts that is holding water. The concrete piping system has several pipe breaks causing misalignments. The backups will continue over time. As the sewer line runs under the garage, it should be fixed permanently before excavation is required. Scheduled to return Tuesday June 22 2021 to install the new sewer liner. 50% paid today with the remainder due at time of job completion. 25% mobilization fee should the job be cancelled.
Today I came to Julieâ€™s Altador home because there was no hot water. Upon diagnostic I found the boiler had shut off on e4 error indicating flame failure. I found the ignition and flame rectification systems are failing. The heat exchanger is badly soiled and must be cleaned. There is a leak internally on a sensor port as well as externally on the thermostatic mixing valve. The under floor heating pump has a failing impeller and is loud. The water softener is almost over flowing with water indicating the injector is failing. Julie has also mentioned that the ac has never worked correctly and has has over 10 different contractors try to fix it. Upon inspection of that system I found there is a restriction in the refrigerant and the fan coil unit is starving for air with only 2 small return air grills for 3 tons of cooling. The inside coil freezes after 2 min of operation. Julie would like options for repair and replacement. She would like me to go over the options with her husband Kir
Today I came to Sharonâ€™s Palliser home because she is concerned about her sewer line. She has had root problems in the past. She recently received our flyer and decided it was a good idea to get the sewer fixed. Upon camera inspection I found the sewer still has multiple breaks that are allowing root intrusions. The line is a perfect candidate for a liner and Sharon has expressed that she would prefer not to excavate.
Today I came to Kevinâ€™s Bearspaw home because he has little to no hot water. Upon diagnostic of the 13 year old boiler system I found the main circulation pump has failed causing water to boil within the boiler itself. 2 of the 3 other pumps are over amperage meaning they will fail. The internal leak on the boiler supply has gotten worse since my last visit and is now dripping to the boiler housing below. The axiom feeder is still faulty and there are several very stiff zone valves. The glycol levels are still slightly low. Tech returned Thursday June 17 2021- Tech Heinz B Tech returned today to install no Taco primary circulation pump with new gaskets. Tech was also supposed to repair a section of 3/4â€ copper pipe in the boiler. After talking with the client we is going to hold off on that section of the repair and is considering replacement. Client was given a quote for one type of boiler system, A Combination boiler. Client also wants a quote for a primary boiler with separate
This call is in the north mount Community,Main Drain is draining at this time ,City was on side and clean the city side on the outside of the property,Client have been charge for td only ,
Today I came to Phil and Tracyâ€™s Dalhousie home because the Ac system is very loud. Upon diagnostic I found the system is low on refrigerant. I also found the the outer cage and covers were vibrating and making the noise. I recharged the system and added additional strapping to the Ac to stop the vibration. The system is now working well and very quiet. Phil and Tracy are happy with todayâ€™s service.
This call is in the South Wood Community,Water Pressure in the house is at 75 psi,hwt 50 gal Power Venting,Appears to be a water leak on the hwt poly b line ,old water line to supply water to the water softener ,Job to do Remove old poly b water line on the hwt,Remove old poly water line water softener line ,supply and install new pex line to reset the water line ,Complete installation,no more leaks at this time,Customer Ratting from 1/10 Customer Ratting is 10.customer is happy and satisfied with the service.
Client called about hot water tank leaking, tech went out confirmed tank does have a micro leak some where under the jacket, water pressure 65 psi normal, new water softener is functional, there is no more manufacturers warranty on the tank as it has been replaced once before. Tech made a few options. Client going with new tankless to be installed tomorrow. Client is happy 10/10