Coady was very pleasant and worked very fast and organized he also would be on the list of workers to return for any future work thank you
$700/hour seems like a lot, but what do I know?
Completed KCM annual club safety and maintenance inspection. Inspected all visible plumbing in the home, tested all toilets, tested all emergency stops, tested all faucets, tightened all under sink drain piping, tested shower, inspected crawl space piping, drained and flushed hot water heater, and tested water quality. The homes plumbing is working as designed with no visible imperfections. The homes hot water heater is a Bradford White 50 Gallon Electric, and is 7 years old. The water heater is working as designed. Water quality report: Hardness- 2 (good) PH- 8 (good) Iron- 0 (good) Pressure 50psi (good) The customer has three bathrooms. All three of the toilets were having issues. Provided pricing to make necessary repairs, the customer accepted the pricing. Replaced the fill valve for the downstairs hallway bathroom while on site, it was making a loud whine when filling. The upstairs bathroom toilet is a Toto brand and parts have been ordered to make the needed repairs
Customer had leak on 1/2 inch gray poly plastic line under hot shutoff in hallway bathroom. Shut water off at water heater and drained pipe. Removed bad section of pipe and replaced with copper pipe and new shutoff. Tested for leaks. Water heater is 19 year old 50 gallon short electric in the closet of bedroom. Did not see any leaks at time of service. Gave pricing for a new 40 electric as this is the only size that will fit in this area. Gave pricing previously to repipe entire home with new water supply piping. Please send hard copy of invoice.
Customer complaint of water leaking off and on coming from t&p from water heater. Replaced t&p and expansion tank under warranty. Once both t&p and expansion tank were replaced I checked for leaks. No leaks at this. Thank you for choosing CPI plumbing and heating.
Customer had a leak around the fridge area that had seeped under laminate flooring. They had pulled up a section revealing linoleum. Leak was found on crimped vinyl icemaker supply that was tied into cold water line for washing machine with a needle valve. Cut out old valve and removed vinyl supply line. Provided and installed new quarter turn shutoff for icemaker and installed new supply line. Turned water back on and tested for leaks. Gray poly plastic water supply lines are original to home and are prone to failure. They should be replaced with new water supply piping in near future to avoid water damage.
Customer complaint of two slow draining bathroom sinks and one slow draining tub, also request to replace tub spout. Gave option for drain cleaning at bathroom sinks and tub and gave option for tub spout replacement. First began with drain cleaning at bathroom tub. Ran super vee and was able to clear up the tub train. Drain cleaned at both bathroom sinks. Removed existing tub spout. Installed new chrome tub spout and sealed up with clear caulking. Tested all three drains. Bathtub and both bathroom sinks are now draining properly. New tub spout is working and operating properly. *Note: There is no warranty on drain cleaning. Thank you for choosing CPI plumbing and heating.
Customer complaint of water leaking underneath kitchen sink. Leak was coming from under sink waste piping. Gave option for under sink waste piping replacement. Removed existing waste piping. Installed new tubular pvc plastic under sink waste piping. Tested for leaks by running water and filling up sink compartments multiple times. No leaks at this time. Cleaned up work area. *Customer to be billed. Thank you for choosing CPI plumbing and heating.
Arrived onsite to perform customers annual safety and maintenance inspection on their triangle tube boiler, tested all components, measurements can be found on attached inspection form, installed the triangle tube recall kit. Cleaned out tf1 filter, cleaned condensate trap. Confirmed operation after servicing the unit. Performed combustion analysis recorded data. All Measurements are within the manufacturers requirements. Thank you for choosing CPI Plumbing and Heating Inc.
Called out to the Nicely residence for a clogged kitchen sink drain line. P-trap had been disassembled by homeowner prior to arrival. Received customer authorization to perform drain cleaning through P-trap opening with mechanical cable. Successfully cleared the drain, then reassembled under sink waste piping. Filled sink basin and emptied to verify drain had been cleared. Ran hot water for several minutes without sink backing up. Upon running the camera down the line to inspect, it was discovered that there were multiple large grease deposits still present. Received customer authorization to run hydro jetter down the line to clear deposits. Successfully cleared the line of remaining grease deposits and ran camera down the line in front of customer to verify line had cleared. Reassembled under sink waste piping and tested for leaks. Filled sink basin and emptied to verify proper flow. The under sink waste piping is free of leaks and the line is now draining properly. Thank you for choo
Customers furnace was not working Provided pricing to run a diagnostic on the furnace to figure out the issue. Use meters to test components, etc. will provide further pricing for repairs. Furnace was blowing cold air. Determined that the thermostat was not sending voltage to the common and W terminals inside of the furnace, Jumpered the R and W wires at the thermostat which gives the furnace a call for heat. With jumper furnace is working properly. Provided pricing to replace thermostat. Customer approved so I performed the work. After replacing the thermostat the furnace was working as it should. Ran furnace through 5 cycles and each time it worked great. Thank you for choosing CPI Plumbing and Heating Inc.
Performed work as proposed Installed commercial pre rinse faucet with sprayer Installed new basket strainers on double compartment sink Installed new basket strainer on triple compartment sink All new plumbing tested no leaks No warranty on any existing plumbing or plumbing fixtures No warranty on any owner supplied fixtures
Performed work as proposed. Installed owner supplied kitchen faucet with pre-rinse and sprayer. Replaced 5 basket strainers. Tested, no leaks. No warranty on existing plumbing.
Customer complaint of a clog in bathroom. When I arrived there was standing water in the tub, I determined it was a main line blockage. Gave option for drain cleaning through inside clean out, clean out is diagonally behind the toilet. Ran the camera down and first located the blockage at approximately 25 feet. I then ran 300 machine down all the way and was able to clear the blockage. As I pulled the snake back I got to a point where it came back all kinked up. I removed the 300 machine from the bathroom to outside of the home. I then recameraed the line and saw that it came to a septic tank. Customer was under the impression they were on city sewer. Informed the customer they are in fact on septic. Located septic in the back yard. Cleaned up work area. Thank you for choosing CPI plumbing and heating.
****please mail copy of invoice**** Performed repipe of exposed area below floor with new Pex pipe and fittings Tested no leaks No warranty on any existing plumbing
Kitchen Sink Cleaning, Arrived on site per customers request of kitchen sink backing up. Ran 100 machine through the kitchen drain line. Cleared the line and ran water for about 30 minutes, as well filled the sink 12 times full of water and everything drained properly. Put under sink drainage piping back together and checked for leaks. Found none Thank you for choosing CPI plumbing and heating Inc.
Customer called back because of leak on shark bite fitting that was used to repair a leaking cpvc pipe. There was a tiny stress crack where the shark bite coupler had been installed causing a small drip. Removed the leaking section of pipe and reconnected the piping. The leak has been repaired.