Amer was efficient and answered my questions. He also helped me choose the maintenance plan to purchase.
Hobaica does a great job on our semi-annual air conditioning and furnace service checkups.
Surprised when systems are relatively new and 'checked-out' by Hobaica Challenge to get service when HOA precludes service vehicles on site after customary business hours … delays carried over for two days
I have used Hobaica services for the last five years and have not been disappointed.
Prompt and efficient
Waived plumbing service call fee at time of pcp and customer switched to gold tcc, 20% discount for furnace/Ac, from 2009, 10 years old. I Plunged out master toilet to get flowing again. Discussed age of toilet uses more water than normal and water prices are going up a lot. New toilets would save.
Review for Amer
Perform bi annual service for a Lennox gas split system.
Perform maintenance on a Lennox package heat pump. Checked filter, thermostat operation, return and supply temperature, refrigerant pressure, compressor, indoor and outdoor motor amps, capacitor, tightened electrical connections, indoor and outdoor coil, drain pan/line is clear. Unit is running properly at this time. Thank you for choosing Hobaica Services.
Maintenance on a Trane Packaged heat pump. Thank you for choosing Hobaica Services, have a great day! -Ted K
Perform maintenance on 2 daikin split gas/ac units.
1998 Goodman php I replaced outdoor fan motor with 1/6hp 825 rpm rescue motor and removed and cleaned blower wheel and motor. Due to age, #r22 phase out and over all condition I recommended replacing units for more efficient and reliable equipment. Performed maintenance in cooling. Checked coils, electrical, capacitors, controls, safeties, airflow, temperature split, refrigerant pressures, motors and bearings, c
Apache junction for heat pump tune up and back for evaporative cooler belt change due to cracking broke blower cooling belt.
I always check out all the cooling operation and I sometime check out the heating operation and then almost always 99% a time exact science replicate hot load desert conditions for HVAC heat pumps on the roof is very hot in the attic I sure wouldn’t want to go in there, maybe better than a crawlspace
Perform maintenance on a trane and goettl package heat pump.
Air-conditioning maintenance tuneup special spring service roof package heat pump on the roof top unit heating and cooling system operational properly at this time
Commercial maintenance plan (2) 7.5 Ton carrier AC/Heatpump Units & (12) Commercial EVAP Coolers spring start up. 2 adobe air evap coolers are not used, no water, pads, or drain fittings or pipe, should be replaced vs repairs due to their condition. Evap cooler #2 on east roof needs water shut of replaced on roof.
Upon arrival found run cap bad for compressor 80 mfd and wiring burnt up and melted and capacitor. Possible long term damage has been done to compressor and it may have even stated up most of the time and then ran hot due to start cap on system could help compressor start but then it comes out of circuit before it overheats, sometimes compressor will keep running with bad run cap and over amp and overheat. At this time capacitor and wiring repairs are needed to further test the system.
Perform Quality Control Inspection for 2 systems, NO REBATE, NO DT, NO HPT, IVAN/JORGE, install (2) wifi thermostats on new roof a/c units we just installed over the pie area of the church & start up units