Binh is very nice, neat and informative.
Hobaica should be grateful to have Michael represent the company.
danny unglaub came to check out my ac unit . went throught every step he took to service the unit including pictures and video of equipment cleaned the coils and made repairs where needed.great job i would say you have a 1st rate employee.a great asset to your company. thank you for the service.
Danny came for the maintenance appointment promptly. He was very professional and gave me excellent advice. I appreciate him answering all of my questions about my A/C. He was meticulous and thorough in his work.
Danny was polite and explained all the areas that he was checking. He also went over the problems that he found and their possible resolution. I think he did a very good job.
Just completed my seasonal service and the experience was great from scheduling through the service provided by Danny. He arrived when indicated he would, was efficient and friendly and explained what was done thoroughly. Continued excellent service that I have received for the past 14 years or so that I have used Hobaica!
Excellent everything, and as always on time with a smile. Respectfully,
Danny was very efficient, business-like,polite,and informative. He is welcome to check my system again when the time comes. Thank you for sending him.
Tom has always been helpful and friendly and very knowledgeable
In Mesa Arizona completed a scheduled maintenance on a train split furnace and straight cool unit in cooling mode, I inspected the return grill and changed the air filter, engage thermostat in the cooling mode, checked indoor temperatures, checked indoor airflow, checked indoor blower amp draw, no capacitor, checked and cleared drain line and drain pan. Check refrigerant charge, checked compressor amp draw, checked outdoor fan motor, checked all high-voltage connections and dusted off controls
Performed maintenance in cooling. Checked air filter, thermostat, coils, electrical, capacitors, controls, safeties, airflow, temperature split, refrigerant pressures, motors and bearings, compressor and amperages, flushed condensate drain line and rinsed outdoor coil with water. System is operating normally and readings are within manufacture specifications at this time. Thank you for your continued confidence.
In Mesa Arizona, on a customer courtesy car to secure an electrical disconnect box and reattach some sheet metal framing that went around the base of her unit. Also lifted and secured the drain line as it was drooping not allowing for proper drainage. The unit is operating properly at this time thank you for choosing Hobaica!
In Mesa Arizona performing a $49 cooling inspection on a Lennox split furnace and straight cool unit in cooling mode. I recorded and our temperatures, Indoor motor amp draw, inspect indoor coil, inspect drain pan and drain line. At condenser checked refrigerant pressures, compressor amp draw, outdoor fan motor amp draw, inspect outdoor coil, checked and tightened all electrical connections. This unit is operating properly at this time, i got Bruce a roofer to contact
Repair refrigerant leak by replacing liquid line valve on split air conditioning system
New customer special Daikin mini split not cooling properly so I will check it out
In Mesa Arizona, I completed a promotional inspection on two package heat pump units, a train unit and an American best unit. Recorded indoor temperatures, amp draw of all motors, tested all capacitors, inspected all coils, inspected drain pan and drain line, checked refrigerant charge and pressures, tightened all electrical connections. Trane unit had bad run capacitors that I changed out for a TURBO200x 80/10mfd with Merrill’s approval. Both units are now operating properly.
2017 Lennox to stage package heat pump maintenance check up and cooling I also flushed condensate drain line and restart the outdoor coil
arrival met with customer and check d out thermostat. Found thermostat was on off position. I cycled system on cooling at thermostat and went up on roof to performed diagnostic. Found system was running on heating mode while thermostat was calling for cooling. Checked thermostat wires are ok. Replaced thermostat with new one. Cycled system back on cooling ok now
Performed maintenance on Gaspack system. In cooling mode, Checked all electrical components and dusted control boards. Checked temperature splits, static pressures. Checked amp draw on outdoor fan, indoor fan, compressor. Checked capacitor for compressor, indoor fan, outdoor fan. Tighten connections and checked for shorts or other issues. Checked refrigerant pressures, superheat and sub cool. Tested motors for play in the bearings and visually Inspecte
Performed bi annual inspection on a wine cellar refrigeration system. Cycled system in cooling and checked refrigerant pressure, electrical, motors bearing, amp draws, runcaps, coils, temperature, condensate drain and pump down operational. Found system is operational properly within manufacture specification. Performed plumbing inspection. Checked and exercised all angle stop valves. Tested water pressure supply to the house is 60 PSI. Found the two angle stop valves for wet bar plumbing
Performed bi annual service for wine cellar refrigeration system. Cycled system on and checked operational, system pressure, amp draws, run cap, coil and pump down operational. Found system is operational ok at this time. Thank you for choosing Hobaica services.