I had a complex HVAC replacement with difficult attic access. Hobiaca team arrived on the day we had agreed and performed the install flawlessly. Greatly appreciate the meticulous workmanship especially on an extremely hot day. And also greatly appreciate sending the contractor out to perfectly restore trim around the attic hatch that needed to be removed to perform the install. Five star install.
Been working with Hobaica since we moved into the area in 2018, and have used them for plumbing, water filtration, running gas lines for an outdoor kitchen, and now a full AC replacement. Very satisfied every time, will continue to use them for all our plumbing and AC needs!
Job well done, very professional.
Jorge and Jason were so polite and respectful during the time they were here installing a new air conditioner. They answered all my questions. They worked in the rain and cleaned up after themselves. As they said, “We want to leave your house looking like we were never here.” And that they did. GREAT JOB guys!!!
Great service and professionalism from Travis.
We have enjoyed consistent service from Hobaica since the early 1990’s. They have never disappointed us. Our latest visit was by Technician Michael Varela who presented himself in a professional manner and a good reflection on his company.
Great service with honest genuine care and understanding for their customers.
Mike did a through job. Thanks
Excellent, timely, knowledgeable and professional service employee.
New package unit AC . On rooftop new cut in new thermostat
New Lenoxx HVAC system , removal of old unit and ERV. New icomfort s30 thermostat... installed by Gio and Jason
New hvac system .. (Gio/Troy)
Condenser fan motor
Performed maintenance on a Trane package heat pump
Trane package heat pump
Performed maintenance in cooling. Checked air filter, thermostat, coils, electrical, capacitors, controls, safeties, airflow, temperature split, refrigerant pressures, motors and bearings, compressor and amperages, flushed condensate drain line and rinsed outdoor coil with water. System is operating normally and readings are within manufacture specifications at this time. Thank you for your continued confidence.
Perform scheduled commercial maintenance service on equipment in heating mode. Changed out filters with pleated tape. Inspected refrigerant pressures and amp draw capacitors controls temperature split belts motors bearings coils reversing valves and disconnects. Cleaned out control compartments. Tightened contactor connections. Noted that building C condenser is not operating in heating mode due to a restricted expansion valve. This unit is a 2002 model and utilizes phased out refrigerant.
Be Daikin inverter system installed by jorge
New 4 ton furnace , coil , t1 thermostat new condenser 230 v
Split daikin system