Jorge and Jason were so polite and respectful during the time they were here installing a new air conditioner. They answered all my questions. They worked in the rain and cleaned up after themselves. As they said, “We want to leave your house looking like we were never here.” And that they did. GREAT JOB guys!!!
Great service and professionalism from Travis.
We have enjoyed consistent service from Hobaica since the early 1990’s. They have never disappointed us. Our latest visit was by Technician Michael Varela who presented himself in a professional manner and a good reflection on his company.
Great service with honest genuine care and understanding for their customers.
Mike did a through job. Thanks
Excellent, timely, knowledgeable and professional service employee.
Danny was very thorough and competent. His attention to detail exceptional.
Danny from Hobaica was Excellent Service and Very Thorough and Efficient.He explained everything and caught an issue with our Primary & Secondary Pans with Water .Highly Recommended from our Family .Great Job Danny !
Jorge and Ethan did an outstanding job with removal of old unit and installation of new A.C. Unit
Trane package heat pump
Performed maintenance in cooling. Checked air filter, thermostat, coils, electrical, capacitors, controls, safeties, airflow, temperature split, refrigerant pressures, motors and bearings, compressor and amperages, flushed condensate drain line and rinsed outdoor coil with water. System is operating normally and readings are within manufacture specifications at this time. Thank you for your continued confidence.
Perform scheduled commercial maintenance service on equipment in heating mode. Changed out filters with pleated tape. Inspected refrigerant pressures and amp draw capacitors controls temperature split belts motors bearings coils reversing valves and disconnects. Cleaned out control compartments. Tightened contactor connections. Noted that building C condenser is not operating in heating mode due to a restricted expansion valve. This unit is a 2002 model and utilizes phased out refrigerant.
Be Daikin inverter system installed by jorge
New 4 ton furnace , coil , t1 thermostat new condenser 230 v
Split daikin system
Water heater flush
Unit MONTHLY TCC SILVER 1 UNIT BI-ANNUAL INSPECTION
Maintenance on split furnace system
Package heat pump maintenance
Leak repair on second floor Lennox condensing unit