Simon P. was awesome. He went out of his way to help with reconnecting my dryer vent when no one else would and he made very needed and helpful suggestions.
Simon was very knowledgeable and informative
The new unit is in (11:00 AM) and functioning. The guys who did the work were very pleasant and helpful. They were efficient and good at what they were doing. Great job. I would give them a good review. Ivan Pacheco and Richard Bartynski. Richard was particularly good about showing me how to run the thermostat.
We recently had a heating issue with a newly installed split system. Turned out the copper lines needed some rework. Ethan and Gabe showed up promptly, worked fast but most importantly, maintained a consistently high degree of workmanship throughout their repair. Hard to find good help these days, but these guys are the real deal. Thank you!
Amer was very helpful at our annual service visit. He fixed a few minor things, suggested some items that we might consider in the future, and explained the warranty options in a way that made our choices very clear. Much appreciated.
Tom got here promptly at 10AM and left at 1PM Did his usual great work. Never a problem with tom or Hobaica.
Amer Khudher was very friendly and did a good job on servicing our unit.
Service Technician was professional and courteous. I was very pleased with his service and request he service my equipment in the future.
Customer paid water heater flush and water heater repairs on previous invoice. Corrosion and rust on ball valve water heater shut off and it was leaking a little, anode rod was completely deteriorated and Customer approved replacing both. Flushed out water heater tank refilled and it is back up and heating properly now. Please see attached estimate for water softener including one option with carbon filter and a salt free option.
Performed biannual maintenance on One gas pack and one package heat pump systems. Checked: Electrical connections Amp draws Capacitors Motors Bearing wear Coil condition Controls Thermostat operation Temperature split Static pressures Changed filters with customer supplied Cleared condensate drain line Duct seal at unit Refrigerant pressures Tested combustion Cleaned flame sensors Dusted burners and controls Upon inspection
MONTHLY TCC SILVER 1 UNIT BI-ANNUAL INSPECTION (8-12 arrival time) **scheduled with complimentary plumbing inspection**
Warranty 1st Year (4-7- arrival time) AIR BLOWING BUT NOT COLD, SET TO 75 DEG 83 IN THE HOUSE, BREAKER HASN'T BEEN TRIPPED **there is a separate plumbing ticket for water heater down**
Performed $69 service special on 1 Lennox package heat pump and 1 trane package heat pump. Checked filters and thermostat operations, checked return and supply temperatures and static pressures, checked compressor operations and refrigerant pressures in cooling, checked compressor amps and outdoor motor amps and indoor motor amps, checked capacitors and tightened all electrical components, both indoor coils are clean and outdoor coils are clean, drain lines/pans are clear. Both units are running pr
Danny performed summer maintenance on David and Melanie’s package furnace. And there was NO DISCREPANCIES!!!
Spring Service (8-12 arrival time) 1M/5HRS - $419.30 tech to collect or ok to bill [2 roof top PKG units & 4 EVAPS] **no filters**
Performed gas pack maintenance in cooling. Checked air filters, thermostat, coils, electrical, capacitors, controls, safeties, airflow, temperature split, refrigerant pressures, motors and bearings, compressor and amperages, System is operating normally and readings are within manufacture specifications at this time. Thank you for your continued confidence.
Warranty 1st Year bedroom system not cooling or getting as much airflow as all other rooms
Danny performed a summer maintenance inspection on Stephanie’s package heat pump.. thank you choosing Hobaica!!
Danny performed maintenance on Connie’s package heat pump
Performed maintenance on package heat pump. Replaced filter with van stock 20*25. Checked: compressor amp, capacitor, thermostat operation, temperature splits, drain line,outdoor motor amp,coils,indoor blower motor amp, clean, tightened all. Left operational Thank you for choosing Hobaica services
MONTHLY NWW TCC GOLD 1 UNIT BI-ANNUAL INSPECTION & PLUMBING INSPECTION (8-12 arrival time) AND SUMMERIZE THE SWAMP COOLER FOR $69
Performed service on a evaporate cooler on the roof. Met with tenant and discussed the work to be completed today. Proceeded to the roof to inspect and run equipment. Inspected float,filll valve, belt, bearings,pully, amp draw, cooler pads, duct connection, pumps, motor, and control. Adjusted float level, set belt to proper tension. Cleaned compartment. Oiled blower wheel bearing. The evaporate cooler is operating properly without issue. Thank you for choosing Hobaica services.