Best a/c service ever. Binh climbed into the ceiling and and down several times over 2 days and was able to get cooling on the second. He had everything working today.
Binh came out same day and was able to fix our HVAC unit by swapping out the capacitor in exquisite time!
I would definitely use this company again! Excellent job!
Brandon arrives on time, completes his work efficiently and with minimal impact on household, and provides all the information about current condition of our system and any possible future maintenance needs.
Brandon has performed our bi-annual tune-ups several times now. I am always pleased with his service and his caring personality. He is great with the kids, and we all feel at ease having him in our home.
Brandon always arrives on time, takes great care when he is inside the house (booties on shoes, etc.), and provides us with complete explanations about any service issues he finds. We have a service agreement with Hobaica, and heavily rely on their expertise to maintain our systems at top efficiency and to ensure system longevity.
Twice a year, Hobaica technicians come to my house to perform maintenance on our A/C unit. Brandon, the Hobaica representative, was very professional, friendly, and always looking out for our family. Thank you for taking such great care of us!
Brandon is very knowlageable about his work
We've been customers of Hobaica for a couple of years, and rely on them to check out our HVAC system twice a year. They are always professional and respectful of our home, both inside and out. Brandon has visited our home twice, and is always knowledgeable, thorough and efficient. We are very particular about which service providers we invite into our home, and are confident we will be Hobaica customers for a long time.
Pleasure to meet Brandon for the first time. He did a thorough inspection of my units. Looking forward with working with him in the future
performed gas heating maintenance, performed full combustion analysis, cleaned burner assembly, inspected flame rod, igniter and safeties, measured airflow and temperature rise and blower motor operation. Equipment is operating properly and readings are within manufacture specifications at this time. Thank you for your continued confidence.
Air filters badly need changed more often, I highly recommend duct cleaning for each system which incudes cleaning the indoor coils and entire blower assembly, condensate drain pan and drain line as well as the clothes dryer vent. Additionally I found there is rust in the emergency drain pan of the older trane unit located in the attic, I recommend adding a condensate safety flood preventer switch inside of this pan to help make sure no more water gets in it. Please see attached estimates, customer stated her husband will let us know about duct cleaning and the condensate safety, she declined both for now.
Replace control circuit board for Amana air handler.
Perform diagnostic and repair on a split system.
Perform bi annual service.
Perform bi annual service on two carrier gas split systems.
Last four serial #7113. Upon arrival met with Bryce and he said he the upstairs system out door unit did not come on. I went out back and checked out door unit and found system is ok. Found breaker tripped. Checked lugs and found they were loose. Tighten up lugs at breaker and cycle system back on. Checked system operational and found system is operational ok at this time.
Inspected unit in cooling Checked refrigerant levels pressures temperature difference between supply and return static pressures visual inspection for refrigerant leaks checked motor
Found bedroom side system low on r410a, I completed visual and electronic leak search and did not locate any leaks. System took 5 lbs r410a to get back to factory specs and cooling and heating well again at this time. Outdoor Serial 5817b10136 and indoor serial 1617F02860. System may have leak that if becomes worse we can find and repair. Systems are now both operating properly and ready for winter. Thank you for your continued confidence.
Inspected unit in cooling Checked refrigerant levels, pressures, temperature difference between supply and return, static pressures, visual inspection for refrigerant leaks, checked motor bearings, capacitors, contactor, amps, flushed condehnsate line, cleaned condenser coil. replaced filters. Replaced monthly perferred maintenance monthly with silver total care club monthly since it’s better than our old perferre
Perform bi annual service on two Lennox gas furnaces.
Perform pcp 3 unit maintenance. Checked electrical and mechanical controls. Inspected compressor operation and refrigerant pressures. Inspected and tightened electrical connections. Checked outdoor fan motor and bearing. Inspected outdoor coil. Inspected indoor blower and air handler section. Checked drain pan systems operating properly at this time.
Completed services two gas split systems. Cycle system on heat/cool and checked refrigerant pressure, electrical, motors bearing, amp draws, run caps, temperature split. Performed combustion test on both furnaces. Checked condensate drain and pump are operational ok. System is operational within ,anifacture specification. Recommend to install low level CO monitors.
Performed pcp maintenance in cooling. Checked air filter, thermostat, coils, electrical, controls, safeties, airflow, temperature split, refrigerant pressures, motors and bearings, compressor and amperages, flushed condensate drain line and rinsed outdoor coil with water. System is operating normally and readings are within manufacture specifications at this time. Thank you for choosing Hobaica!