Issac came and concord our Hvac problem.
As always very wonderful!!
I came out to check system over. After a miscommunication with the diagnostic fee, we waved it today. They have replaced the condenser fan motor and contactor. But the system still wasnâ€™t running. The system is getting 24v to the contactor, but itâ€™s not closing. I gave the, a price to replace it. But sheâ€™s going to take back the one they put on and swap it out. I told her when they get the new one to call us for her AC maintenance and weâ€™d out her contactor on for free. I left the disconnect off.
Came out for an estimate for a property management company. 5t system. All equipment and copper stolen. Electrical wire cut at closet base.
I arrived for a non membership no cool call. I inspected the indoor system and found the evaporator coil to be clean but rusted. I also found all components in the furnace to be in work condition. I inspect the filters and found the pleated filters to be bowing in. This systems return is undersized. I inspected the conditioner and found the systems to be running low on refegerant charge. I recommend to have the return duct increased and to have a leak search preformed on the system. We decide to charge the system to get it running properly and see how it runs throughout the summer. This system is running and working to the best of its ability at this time.
I arrived for non member no cool call. I first spoke with the homeowner and found the issue to be the outdoor unit to not be running. I inspected the outdoor system and found the compressor and condenser fan motor to be overheated. I also found the condenser coil to be completely stopped up and the capacitor to have failed. I then installed the indoor unit and found the the evaporator coil to be dirty. I recommend to replace the capacitor and clean the evap coil. We decided to replace the capacitor and add a hard start kit to the condenser. I cleaned the conditioner and cycled the system on. I found the super heat to be running at 12 deg. The system calls for 14 deg super heat. This system is runs to the best of of its abilities at this time.
Caller canceled call before my arrival
Came out to call. Customer said system just stopped working all of a sudden and couldnâ€™t figure out why. I checked system over and found the system not communicating with the air handler. Inspected air handler and found the 3 amp fuse blown. Put a resetable fuse in and turned power back on. As soon as I did the UVC lamp we installed recently made a strange noise and was putting off a burning smell. Further inspection led me to the internals of the UVC lamp having a short in it, causing the fuse to blow. I replaced the 24 volt UVC lamp under warranty. Seeing that Iâ€™m out here, I went ahead and performed the tune up as well. Checked thermostat operation, wiring, capacitor, contactor, compressor, amps, temperatures and pressures. Discussed with customer about about the system being a tad low on refrigerant. Added 1.4 lbs of 410a to get charge correct. System is cooling properly within manufactured specifications at this time.
Duck cleaning home that has recently gone under renovations and remodeling.
Perform blue shield protection plan furnace maintenance
Serviced a Lennox and a carrier system for winter operation. Installed a capacitor and a uv light.
Duct cleaning for home with some bacterial growth in vents.
Preformed AC maintenance on a 2011 Lennox system
Duct cleaning home with 13 supplies and 3 returns.
Preventative Maintenance Service on Comfortmaker 7 year old Residential package unit
Duct cleaning with Red Shield Protection Plan AC scheduled tune up. Three year old Carrier Air Handler and Heat Pump zoned system.
Goodman AC not cooling properly. Capacitor replacement needed. Preventative Maintenance Service Suggestion