Being on program well worth it.
Adam our tech went above and beyond to get our AC running again. The whole team is very friendly and helpful.
Issac came and concord our Hvac problem.
As always very wonderful!!
Preformed heat pm on 4 ton hp zoned system checked amps on all motors and they where within spec compressor running 9.5 a of 20 capacitor read within spec and hp operation was correct customer changes filters regularlyðŸ˜ðŸ˜ the return air was correctly sized. The system is operating correctly at this time and our records show you are eligible for duct clean in one year. Discussed earlier recommendations and the customer is still considering them.
Came out to call. Customer stated that the system stopped working all of a sudden and was only blowing cold air. The heat pump wouldnâ€™t work, nor was the auxiliary heat. I checked system over and found a blown low voltage fuse. The last time this happened it was due to the 24 volt uv lamp. I checked the lamp and found it to be the culprit again. Iâ€™ve already replaced it under warranty before, but we have a newer model now. Told customer I would have to come back out to replace it under warranty again. Customer stated that itâ€™s not an emergency, and can be done on his next service.
Preformed fall service on variable speed heat pump checked amps on motors and elements they where good capacitor on compressor 28.8 of 30 customer informed me they have replace warranty capacitor a couple time the system is 6 years old. Tested operation of heat pump and took the top of and washed the coil the indoor coil was clean I asked customer if there where Rooms that were too hot or too cold or didnâ€™t get enough air in the customer said yes and then explain to him how static pressure works and expressed how the ductwork was incorrectly installed and why there was lacking air in places also found kinked of ducks and 4 splices with no support a.k.a. a ghost splice I found a 8 inch duct with a ghost splice into a 12 inch duct I recommend having all ductwork cut loose dampeners installed all ghost seams undone and correct splices put in turn the 8 inch duct into a 12 inch duct and re-run it seal up the Plenum where it goes to stop attic air from being sucked into the system to reat
Inspect home for duct cleaning. Spoke with tenant, and main issue was in the last several weeks the house had gotten very dusty and it was difficult to breathe. After investigating further I believe the issue was some workers had been in the attic to do some work on a shower installation, and had disturbed the insulation in the attic. The fine insulation particles were getting through large joints at the supply boot elbows and giving the tenant that gritty itchy feeling that they were dealing with. Recommend a level one cleaning on ductwork, seal those joints, clean supply vents and grills, wipe away loose popcorn texture, and spray and disinfectant spray. Went over details with homeowner and she approved recommended cleaning. Lea drop sheets were necessary, removed vents and grills. Cleaned out popcorn texture overspray in supply boots as best as possible. Sealed open joints at supply boot elbows. Duck cleaned Supplies with 3 to 4 passes each. Duck clean return cavity. Vacuumed out f
I arrived for a blower membership fall maintenance. I first spoke with the homeowner and found no issues with the upstairs system. I preformed a full evaluation on the furnace in low and high stage heating. I explained how the system runs and showed the homeowner the benefits of having a two stage system. Overall this system is running properly at this time.
I arrived for a ac tune up for a club member. I first inspect the system and found the capacitor on the compressor to be completely depleted and not operating at all. I recommended to repair the capacitor under warranty to limit stress on the compressor. I also found the indoor system to be covered with growth. We decided to replace the capacitor at this time. I will follow up with the homeowners about the whole house air purification system Wednesday.
Gave customer estimates on a 20 and 19 Seer Complete 4 Ton System. Keeping and flushing existing lineset. Customer stated that the returns were undersized and also wanted information on air cleaners as well. I made recommendations and discussed the differences. Ended up adding the polarized air cleaner, whole house germicidal purification system, and HEPA air cleaner to estimates. 2 main returns will be expanded to 16â€ and the 10â€ in the master bedroom will stay the same. We will add a 20x25 filter cabinet to furnace for the polarized media.
I arrived for a silver member ac pm. I first spoke with the homeowner and the only other issue as they wanted the heating checked out for winter. I first inspected the heater and found no issues with its operation at this time. I then inspected the ac and found the condenser coil to be stopped up. I cleaned the condenser coil and all electrical components and found the capacitor to be weak and out of manufacture range of operation. I also found the contactor to be starting to blacken and pit. I made all issues aware to the homeowner and we decided to replace the capacitor at this time and we are planning on replacing the contactor on next summer tune up. I checked the systems refrigerant charge but the out door temp was 63 deg. The subcooling at this time was 9.1 deg. I found no other issues with this system at this time. I preformed both heating and cooling pms at this time.
Inspect home for duct cleaning. Customers just purchased home about 2 weeks ago and are looking to have ducts cleaned due to a heavy amount of dust in home. Home built in 2013 and has original HVAC system. Inspect evap coil and drain pan. There is a drip in rear of air handler and coil over drain pan and a leak in the pvc behind the unit due to 2 45 degree joints not being glued or primered. Checked unit level and and drainage and with customer permission, repaired drain line and flushed system with nitrogen to ensure proper flow. Also set level to to drain towards main drain. Layed drop sheets where needed and cleaned 18 supplies and 3 returns. One return was cleaned at no charge due to it not having more than 2 feet of run. Removed filters, grills and vents and cleaned with spinning brush and microfiber cloth. Cleaned ducts with 3 to 5 passes each. Upstairs vents were not tied to studs so replaced them as is and held ducts through cleaning. Sprayed in hospital grade disinfectant sp
23JUL20-I came out for a no cool, on the upstairs system. I ch3cked the system over and found the bearings in the variable speed motor have locked up. The unit is still under parts warranty. I will call carrier in the morning and order the motor. Then hav the office call and schedule a time to return to install it. We will complete the AC maintenance when we return to install the blower motor. 24JUL20-I returned with the new motor. I installed the warranty variable speed motor and wired it in and completed the AC maintenance. I washed the AC coil. I checked the filter, evap coil, drain, capacitor, contactor and all wiring. I cycled the AC and checked all temps, amps and charge. All working well.
I came out for a blue plan ac maintenance. They got their contactor changed out and the system is cooling. I washed the condenser coil. I checked the blower, evap coil, capacitors, contactor and all wiring. I cycled the ac and checked all temps, amps and charge. The system is working like it should. I recommend saving for a new system, due to its age.
I came out to check system over. After a miscommunication with the diagnostic fee, we waved it today. They have replaced the condenser fan motor and contactor. But the system still wasnâ€™t running. The system is getting 24v to the contactor, but itâ€™s not closing. I gave the, a price to replace it. But sheâ€™s going to take back the one they put on and swap it out. I told her when they get the new one to call us for her AC maintenance and weâ€™d out her contactor on for free. I left the disconnect off.
Came out for an estimate for a property management company. 5t system. All equipment and copper stolen. Electrical wire cut at closet base.
I arrived for a non membership no cool call. I inspected the indoor system and found the evaporator coil to be clean but rusted. I also found all components in the furnace to be in work condition. I inspect the filters and found the pleated filters to be bowing in. This systems return is undersized. I inspected the conditioner and found the systems to be running low on refegerant charge. I recommend to have the return duct increased and to have a leak search preformed on the system. We decide to charge the system to get it running properly and see how it runs throughout the summer. This system is running and working to the best of its ability at this time.
I arrived for non member no cool call. I first spoke with the homeowner and found the issue to be the outdoor unit to not be running. I inspected the outdoor system and found the compressor and condenser fan motor to be overheated. I also found the condenser coil to be completely stopped up and the capacitor to have failed. I then installed the indoor unit and found the the evaporator coil to be dirty. I recommend to replace the capacitor and clean the evap coil. We decided to replace the capacitor and add a hard start kit to the condenser. I cleaned the conditioner and cycled the system on. I found the super heat to be running at 12 deg. The system calls for 14 deg super heat. This system is runs to the best of of its abilities at this time.