Performed an inspection, and performed all repairs same day!!
The price was awesome and our house is cool and again! Thank you for your speedy service!
On October 5, 2021 arrive to a previous customer nonmember upon arrival I greeted the customer they stated that the fan motor wasnâ€™t kicking on and the coils not condensating went to the condenser fan motor after starting the system spun it fired up pulled the disconnect check the capacitor it was parked changed out the capacitor with customer permission tested it system started immediately did amp drawls on the compressor check the charge and then went inside and check the air everything is working properly at this time thank you for your business Mike T
I arrived for a no heat call on a mobile home propane furnace. I inspected the furnace and found the induced draft motor and pressure switch assembly to be locked up and not allowing the furnace to cycle on. I hand spun the motor and found it to be rusted at 0.56 amps and the limit it 0.55 amps. I recommended to replace the assembly of the motor and pressure switch. They are in between purchasing the property and want to get ahold of the previous owners to fix the system before they move locations.
Arrived on the 23rd September for an air-conditioning maintenance re-inspected the blower and evaporator I clean those two last visit I was there and condenser checked drain line checked contactor and capacitor and hard start kit checked Bridget level if I the reason superheat with 20Â° of sub cooling it is fixed orifice system everything is running as it should.
On August 10, 2021 arrive to a new customer nonmember upon arrival I greeted the customer went to the thermostat and turn the system on are they went to the air handler and found that the suction line insulation as well as the front of the air handler was coded in oil opened up the evaporator coil and found that the evaporator was leaking were the copper to aluminum Kâ€™NEX will have to call American standard to check warranty status on unit and then get price and check availability of coil for repair thank you for your business Mike T
April 2 arrived to do an AC and heat p.m. found evaporator was extremely dirty as well as a blower customer authorized cleaning of the evaporator and blower and added pan treatment into the into the drain pan tested everything everything checked out clean clean heat pump changed filters customer provided.
On march 22, 2021 I arrive to a previous customer nonmember to install a new contactor and to test out the system and verify that it work properly I checked capacitor it read good did amp draws everything checked as is supposed to unit is running properly at this time thank you for your business Mike T
Inspect rental home for duct cleaning. See attached photos. System is up flow in garage and is open to garage. Most tenant odor issues are because system is open to garage and has air leaks. Ducts do need to be cleaned. With homeowner approval will be back Weds March 10 2021 to clean ducts seal return plenum and add hospital grade disinfectant spray.
I arrived to inspect the complete duct system. I found the 3.5 ton system to be running on 1.5 ton of return inlet air. I also found duct work to be taped off the top of the supply plenum not allowing the system to build up the proper static pressure the system needs. I showed all my findings to the homeowner and explained that with the system installed the way it is the only way to correct it is to change the position of the system and set the ducts correctly on the plenum and to rerun the duct to all rooms. We decided to replace the return duct to get the proper amount of air to the system to feed the supply duct. The supply duct is incorrect as well. We decided to increased the return duct for now and see how the system operates with the improved return duct. Will need 3 bags of 16â€ duct 2 16â€ stick taps and 2 16â€ finger savor taps.
Previous customer two heat pump and air handler heating tune ups. Customer just head home built last year. Asked about how systems were working and filters. Northwest corner bedrooms struggle to keep up with doors closed, explained how adding crossover grills over the doorways or junction returns in the bedrooms would allow for better air circulation, and that with doors closed, the air isnâ€™t able to be moved the way the system is designed to move it. Inspected both air handlerâ€˜s, blowers, sequencers, heat strips, ductwork, attic insulation and dryer vent. Inspected heat pumps, compressors, fans, capacitors, reversing valves and defrost modes. Checked heat rise in heating and emergency heat modes. Checked refrigerant pressures. Went over cost savings between heating and emergency heating modes. Also talked about our UVC lamps for both air handlers and our shield protection plans. Both systems working well at this time!
Performed silver club air conditioner maintenance. Customer recently replaced filters. Washed condenser. Test capacitor and motor amp draw. Refrigerant levels are in range. System is cooling at this time.
I came out for an estimate on a double wide mobile home. The system is getting older and in fairly poor condition. I recommended replacing full system due to its age, it is undersized for the house and it uses r22 refrigerant, which has been phased out. The crossover duct under the house is completely gone and a lot of the insulation under the house is missing. Either animals or other issues have caused the insulation to be torn out. We can install a new hard pipe cross over, but canâ€™t insulate under the house. It will need to be insulated and have the vapor barrier installed or the ductwork will sweat and can cause water damage.
I came out and inspected the ductwork. The trunk line is ran correctly and in place, from what I can see. Kianoosh needs to come out with the camera and inspect the whole run and quote a duct cleaning and boot replacement/sealing. This is a perfect house for our duct lining. Will have office call in the morning to schedule a time for us to come back out. 5/27/2020 Came out for video inspection of ductwork to get a proper diagnosis. After inspecting each boot and scoping down trunk lines as well as adjoining flex duct, found 1 mouse corpse inside flex duct and removed and reattached flex duct under house to remove it... went under home and found no tears in flex ductwork. Several boots do need to be retaped / repaired / sealed in order to optimize airflow. See attached estimate for work to be done. After getting customer approval to proceed with work, will also give 10% off work and perform complimentary summer ac tune up per service manager request. Washed condenser, cleaned evap
04-27-2020 I arrived for a free secondary opinion. I spoke with the homeowners and found that the systems line set has been cut and pressure tested with the evaporator coil still in the pressure test. I inspected the indoor and outdoor systems and found the line set and evaporator coil to not have any pressure in the coil. I recommend to let me re pressure the lineset and evaporator coil to check for leaks my self. The homeowners agreed. I pressure the evaporator coil and looked for a leak with a electronic leak detector and bird dog leak detector. I found the evaporator coil to be leaking on the front of the coil just behind the face plate in multiple spots. We decide to wait and check on the systems warranty in the morning and to get pricing on replacement the evaporator coil and reconnecting the system. As well as recharge the systems correctly. I am placed this call on hold untill I can contact the homeowner about repair options.
Duct replacement, duct strap up and duct cleaning.
Inspection for duct cleaning