Brandon is very courteous and knowledgable.
We had a tune up service today with Issac. He did a great job. Very professional.
Arrived to no cool service call system under warranty. Found bad 25 amp fuse. Replace fuse. Tested all amp draw. Cycled unit multiple times. System is operating as designed at this time. Found no reason at this time fuse should have blown. Will leave ticket open to see if unit fails again. Set up appointment for Friday July 10th to have maintenance to both systems performed.
I arrived for a no cool on a newly installed system. I spoke with the homeowner and and the main issue was the house keeps getting hotter the longer It runs. I inspected the system and found the Eva coil to be frozen over. I turned the heater on to melt the ice. I inspect the outdoors system and found the solder joint on the high side service valve to be leaking refegerant. I pumped the system down and fixed the leak. I pulled a vacuum and charged the system to run at 11.6 deg subcooling and the system calls for 12 deg subcooling. I added 4.4 LBS of 410A. This call is under warranty.
Maintenance Service on Residential Carrier Heat Pump Systems. Electric Emergency Heat Back up
Install a new Honeywell T-6 Thermostat
Install new capacitor to indoor blower motor on Coleman furnace
2 system Lennox AC summer maintenance.
Carrier Residential AC not cooling properly. Filter needs changing. AC maintenance plan needed
Mobile home AC tune up on an Armstrong air conditioner.
Perform an ac tuneup
Duct cleaning of supply vents for home.
Full system AC coil and furnace change out duct cleaning
Armstrong AC not cooling. Replace bad dual capacitor
Repair the air conditioner
Clean and check 2 systems make ac equipment more efficient