Excellent service. Very professional.
Brandon is very courteous and knowledgable.
We had a tune up service today with Issac. He did a great job. Very professional.
Performed preventative maintenance on 2 heat pump systems for customer. Replaced both systems filter with a fresh new filter for customer. Inspected both air handlers, blower assemblies, evaporator coils, electrical components, heating elements, wiring, and overall condition and operation of air handlers. Cycled emergency heat on both systems and checked amp readings on the heating elements and blower motor. Cycled both heat pumps on and checked operation, amps, temperatures and pressures of both heat pumps. Tested defrost mode and reversing valves. Both systems are heating properly within manufactured specifications at this time. Recommended a duct cleaning to customer.
Came out to call. Customer stated that the tenants to her that the system wasnâ€™t heating properly. They moved into the rental property in November. I checked system over and found the furnace running in lockout, and the fan was running continuously. I checked filter and found it severely clogged, and it hadnâ€™t been changed since April. New tenants had no idea where the filter was located or what size. I showed tenant where it was located and how to change it. I also recommended it be changed every 2-3 months. I found the flame sensor also needing to be cleaned. Cleaned the flame sensor and reinstalled it. Cycled system on to test and verify that the furnace is operational. Furnace is now heating properly.
Blue SPP summer AC maintenance on 2 2019 heat pump and air handler systems. Asked customer about filters and hot and cold spots. Customer mentioned being concerned about a fuse that went out on previous no cool call out. Washed condensing units, both units had frogs that had died and heat fused onto the outer surfaces of heat pumps. Removed frogs and wiped down units. Checked both dual capacitors. Checked amp draws and volt drop for fan motor and compressors. Both units are still under warranty and working great at this time.checked evap coils changed filters, and checked drain lines. Also checked breaker box for both units. Tested amps on inside blowers and thermostats. Cycled both systems on and checked refrigerant charge via delta t. Both systems operating well at the low end of manufacturer specs as a new system should be. Talked briefly about our UVV and UVC lamps for air handlers and sent customers email video with more info. Also talked briefly about our surge protectors and
Arrived to no cool service call system under warranty. Found bad 25 amp fuse. Replace fuse. Tested all amp draw. Cycled unit multiple times. System is operating as designed at this time. Found no reason at this time fuse should have blown. Will leave ticket open to see if unit fails again. Set up appointment for Friday July 10th to have maintenance to both systems performed.
I arrived for a no cool on a newly installed system. I spoke with the homeowner and and the main issue was the house keeps getting hotter the longer It runs. I inspected the system and found the Eva coil to be frozen over. I turned the heater on to melt the ice. I inspect the outdoors system and found the solder joint on the high side service valve to be leaking refegerant. I pumped the system down and fixed the leak. I pulled a vacuum and charged the system to run at 11.6 deg subcooling and the system calls for 12 deg subcooling. I added 4.4 LBS of 410A. This call is under warranty.
Maintenance Service on Residential Carrier Heat Pump Systems. Electric Emergency Heat Back up
Install a new Honeywell T-6 Thermostat
Install new capacitor to indoor blower motor on Coleman furnace
2 system Lennox AC summer maintenance.
Carrier Residential AC not cooling properly. Filter needs changing. AC maintenance plan needed
Mobile home AC tune up on an Armstrong air conditioner.
Perform an ac tuneup
Duct cleaning of supply vents for home.
Full system AC coil and furnace change out duct cleaning
Armstrong AC not cooling. Replace bad dual capacitor