Sales person and installer were great to work with. Did as promised
Service was quick and of little pressure. I was given an honest assessment on my air conditioning system with thoroughly explained options on which steps could be taken next. It’s good to have cool air blowing, once again. Thank you!
Customer had us out for blue SPP tune up on 6/19/2020. Customer hearing a louder than normal noise when AC turns in, especially at night. Checked compressor volt drop, contactor, compressor start and run amps, fan start and run amps, blower start and run amps, and cycled system on and off & 5 times. A louder than usual sound could be heard occasionally, but mainly seemed to be the wind coming over the fan blades as the motor turned on. System is running well at this time.
I arrived for a no cool call on a rent home. I spoke with the tenants and found that the system ran in the morning but the outdoor unit will not run. I inspected the indoor system and found the evaporator coil to be clean and in good condition. It looks like the filters are being changed regularly. I inspected the conditioner and found the systems to be overheated and cover with cotton wood. I cleaned the conditioner and cooled the conditioner fan motor and compressor down. I also found the capacitor to be extremely weak. With the system running with a stopping up condenser coil this can cause the system to run hot and make components fail prematurely. I tried to contact the homeowners by phone call and text per the shops instructions and I did not get ahold of the homeowner. I replaced the capacitor to get the tenant cool at this time.
Blue SPP AC tune up. Asked about home comfort levels, and changed out 20x24 pleated filter. Inspected evap coil and blower wheel. Checked drain line and cycled system on to check indoor amp draws. Washed condenser, checked dual capacitor and contactor. Capacitor showing signs of leaking oil, but still working in proper ranges. Cycled system on and checked amp draws and refrigerant pressures via delta t. System working great at this time.
I came out for a no cool. I checked the system over and found the ac completely out of refrigerant. There is a huge oil slick on the condenser coil. The system may be under a 10yr parts warranty. I need to call the manufacturer in the morning to check in the warranty, price and availability of the condenser coil. M#:GSX130361AB S#:1103710413
Inspect home that has been recently renovated for duct cleaning. Check blower wheel in evaporator coil, both need to be cleaned. Filter needs to be replaced, will replace with customer supplied filter. Evaporator coil has a UVC lamp installed. Recommend changing bulb as it looks to be weak. Ductwork is composed of galvanized metal and was duct taped together without screws, it has deteriorated. Recommend replacing screws before cleaning. Furthest back supply vents will need a level 2 duct cleaning, the rest can be completed with level 1. L After going over options, will move forward with duct cleaning only with anti microbial treatment. Duct clean supplies and Shop vac return cavity. Ductwork held together but do not recommend another duct cleaning before adding screws to joints in ductwork, as the duct tape will continue to deteriorate over time. Fog in anti microbial treatment. Replace fresh filter, Test and verify system operating. Vacuum up excess debris and went over details of o
Serviced and replaced a induced motor on a carrier furnace.
Blue shield protection plan furnace tune up in Concord system
Serviced a carrier for winter performance. Replaced filters and cleaned the condenser coil.
Goodman AC not cooling. Dual capacitor went bad. Install new capacitor and wash condenser coil.
Carrier 3 Ton AC Install
Perform system evaluation on 2004 carrier air conditioner, add r410a refrigerant to system
AC repair, customer has a failed compressor on a 2011 Concord condenser and it only had a 5 year warranty. Customer doesn’t want to replace the compressor he wants a new unit
Video duct inspection to investigate dead animal smell in ductwork.
Carrier AC not cooling properly. Evaporator coil cleaning. Drain line cleaning. AC system needs maintenance
AC maintenance on 2009 Goodman heat pump system