Install Carrier 12.5-Ton Gas Pack
System ending in 919D has a bad tensioner and belt. Recommend a bx62 rubber belt with the tensioner. The heat does not work, the limit switch is burnt the hot surface ignitor is broken. The gas is not turned on so don’t even know if unit will fire up Heat exchanger exhaust is very rusty and inducer does not move a lot of air through heat exchanger. Heat exchanger has a hole in it. Because the heat needs extensive repairs recommended new system. Curbing unit sits on is also damaged
TECHNICIANS REMOVED THE OLD UNIT AND REPLACED IT WITH A NEW TRANE 7.5 TON SPLIT HEAT PUMP
Tech is servicing a Trane split system.
Inspect Carrier furnace and AC, changed filter
Full service on a Trane heat pump, changed filter.
Performed inspection on trane system.