David did a great job! Super friendly!
Mark was very thorough and explained everything to me. Was cool he put on the scrubs (or whatever they are called) to cover his shoes. Very pleasant and professional. Good guy.
Smoke alarm batteries
Tech replaced a 150 amp meter base because of a burnt lug. Tech installed a new meter base and a new mast with new overhead wiring and weather head and strain relief eye bolt. Tech installed a new grounding system with two ground rods and grounded to main breaker panel
Meter mast replacement with new grounding system
Installed new exit lights
Installing new dryer plug
Installing new light fixtures in bathroom
Panel service upgrades
Installing new outlets
installed GFCI outlet to protect kitchen outlets per code, installed new 110 volt floor plug off existing basement circuit for living room floor, and replaced 110 volt single pole switch.
Installation of a floor outlet, GFCI outlets and decora switches in Doravile
Installing ceiling fans
Installing outlet, smoke detector, devices, breakers, and bulbs.
Troubleshooting tripped breakers
Outlets and lights in front bedrooms did not work. Found arc fault breaker was tripped. Reset breaker and tested outlets. Found front right bedroom had open neutral. After diagnosis found outlet in cabinet in front left bedroom had a bad connection on outlet. Replaced outlet now outlet and lights are working.
Replace bath fan with light in master bathroom. Install GFCI breaker