Dependable and informative. Completed thorough inspection and provided items to keep an eye on between inspections.
Cole did an outstanding job! We will look forward to using him again for future electrical jobs around the house.
Boat dock inspection
Tech diagnosed and repaired a power outage in the master bedroom and master bathroom. Technician found several issues. A GFCI outlet in the bathroom was wired incorrectly, causing the bedroom outlets not to work. Tech also found that the overhead lighting outlet in the bathroom was wired incorrectly, causing the lights in the bathroom not to work. Tech rewired the lighting outlet box and the GFCI outlet to correct these issues
replace main breaker panel, installed new smoke detectors
replaced GFCI and outlets
install GFCI at existing location.
Installed 50 amp manual transfer switch for generator. Installed new 20 amp circuit for furnace. Replaced burnt 30 amp 110 volt RV plug.