Hobaica provided a prompt quote with a great price then backed it up with a courteous, professional installation. Rich and Angel did a fantastic job installing our new A/C unit. They took the time to explain what they were doing, operation details, and left the worksite cleaner than they found it.
Service Rep has been here before. He is always polite and professional. Explains what needs to be done and make suggestions, etc in a clear manner. He wants to please.
Very professional, pleasant to deal with Thomas and Hobaica. Heating system wasn't functioning this Sunday morning, while Thomas did not find anything wrong, his checking of the system was important and worth it to us.
I would not have anyone else work on my cooling heating systems
Thomas was professional, seemed thorough and explained what the system's status was. Well done
Two split furnace systems
MONTHLY TCC GOLD 4 UNIT BI-ANNUAL INSPECTION & ELECTRICAL INSPECTION (8-12)
2 units split heat pumps Maintenance and tuneup special check heating systems as well as prepare for summer that is for me and check condensate drain line and good idea to monitor system all the time
20-year-old split heat pump system should be replaced due to phase out refrigerant and multiple other issues
Performed maintenance on 2 split heat pump systems Inspected: * Electrical connections * Amp draws * Capacitors * Motors * Bearing wear * Coil condition * Controls * Thermostat operation * Temperature split * Static pressures * Changed filter * Cleared condensate drain line * Duct seal at unit * Refrigerant pressures R410A NO DISCREPANCIES ON ANY PART OF TO
Completed maintenance on 2 split heat pumps.
2 unit maintenance
Completed maintenance on 2 lennox split systems. Checked and tightened electrical connections and components. Checked indoor and outdoor coils and motors. Rinsed off outdoor coil. Flushed and tested both drain lines. Tested leak protection. Needed to rewire the second floor float switch. Checked temp drop and refrigersnt charge. Both air filters are new and clean. ALl readings are within manufacture specs. No reccomendations at this time. Left operational
Noticed both condensate drains where improper and vented before the trap and are both negative pressure drains. also neither system have any type of condensate safeties. Garage system I plugged the improper vent as it already has exhaust vent after trap. Airhandler in indoor closet should be redone to move vent after trap and should add condensate safety float switch to both systems.