Service Rep has been here before. He is always polite and professional. Explains what needs to be done and make suggestions, etc in a clear manner. He wants to please.
Very professional, pleasant to deal with Thomas and Hobaica. Heating system wasn't functioning this Sunday morning, while Thomas did not find anything wrong, his checking of the system was important and worth it to us.
I would not have anyone else work on my cooling heating systems
Thomas was professional, seemed thorough and explained what the system's status was. Well done
As always I received great service from the gentleman who has helped me before. I apologize for not spelling his name correctly - Binh. He was accompanied by another gentleman who was most helpful.
The engineer arrived promptly and was very pleasant. Was able to answer clearly all my queries on air conditioning enabling me to understand 'safety floats' and 'compressor' problems. Happy with his visit.
Completed maintenance on 2 lennox split systems. Checked and tightened electrical connections and components. Checked indoor and outdoor coils and motors. Rinsed off outdoor coil. Flushed and tested both drain lines. Tested leak protection. Needed to rewire the second floor float switch. Checked temp drop and refrigersnt charge. Both air filters are new and clean. ALl readings are within manufacture specs. No reccomendations at this time. Left operational
Noticed both condensate drains where improper and vented before the trap and are both negative pressure drains. also neither system have any type of condensate safeties. Garage system I plugged the improper vent as it already has exhaust vent after trap. Airhandler in indoor closet should be redone to move vent after trap and should add condensate safety float switch to both systems.
Performed SRP seasonal tune up on a split heat pump, we checked cooling operations, system is operating properly. We did offer a few recommendations that will benefit customer and his system. Thank you for choosing Hobaica services sincerely Ron J.
(2) 5 time vertical furnaces change outs and (2) water heater change out
Do maintenance on two split heat pumps, check motor amp draws, check run capacitors, cycle systems in heating and cooling, check temperature splits, static pressures, both systems are working good.
Perform bi annual service on a wine cellar refrigeration system.
Performed pcp maintenance in cooling. Checked air filter, thermostat, coils, electrical, controls, safeties, airflow, temperature split, refrigerant pressures, motors and bearings, compressor and amperages, flushed condensate drain line and rinsed outdoor coil with water. Inverter system control board failure high amps need to replace control board under part warranty
Residential hvac service
Residential hvac service fountain hills
Perform a maintenance inspection on 2 Lennox gas furnaces located in the attic. Check all mechanical equipment and gas components, the systems are operating properly, and are ready for the winter in the fountain hills area.
Perform bi annual service for split system.
Perform bi annual service on two lennox gas split systems.
Performed pcp maintenance in cooling. Checked air filter, thermostat, coils, electrical, controls, safeties, airflow, temperature split, refrigerant pressures, motors and bearings, compressor and amperages, flushed condensate drain line and rinsed outdoor coil with water. System is operating normally and readings are within manufacture specifications at this time. Thank you for choosing Hobaica!