I like how he explained everything to me. He and Hobiaca are terrific!
Well Done - Bought a Carbon Monoxide Monitor
We enjoyed meeting Binh. He did an excellent job this morning servicing our air conditioner unit. He was personable, professional, and very competent. We feel that he went above and beyond our expectations. We would not hesitate to request his services again.
Professional, courteous, and prompt. Brandon drives many miles...
Recommended water heater cleanup and I get hot water in the bathroom now!
The serviceman was very courteous and professional. He listened to my concerns, he showed me what he intended to do to implement repairs, and he made suggestions for follow-up. He was extremely tidy and cleaned up after the work was finished; I'm always thankful for conscientious repairmen. I am quite pleased with the results of the work.
Performed pack heat pump maintenance in heating. Checked air filter, thermostat, coils, electrical, capacitors, controls, safeties, airflow, temperature split, refrigerant pressures, motors and bearings, compressor and amperages, System is operating normally and readings are within manufacture specifications, ready for winter. Thank you for your continued confidence.
Performed condensation drain line repair, I added 20’ of 3/4” pvc and fittings to properly drain the condensation from the air conditioning system. Systems condensation drain line is properly draining and secured. Thank you for choosing Hobaica services, Ron J.
Whole house air conditioning, electrical and plumbing inspection I replace the hose bib out front because it had no threats and hers was stuck on
Rebuilding main manifold
Rebuilding main manifold
Review for Amer
Perform service on a gas split system.
Performed maintenance on a daikin gas furnace. Checked filter and thermostat operations, checked return and supply temperatures and static pressures, checked burners and flames and safety switches, completed combustion analysis and checked heat exchanger, checked indoor motor amps and bearings, indoor coil is clean and drain line/pan is clear. Unit is running properly at this time, thank you for choosing hobaica services.
Diagnostic on split furnace. Indoor is running outdoor unit is not running. Checked condensate float switch is tripped drain line is not clogged. After further inspection found safety switch threads are stripped and switch is defective. This particular switch is not one we install, however we do offer a different type of safety switch. Quoted to replace switch at 280.06 customer approved he also has a 50.00 off coupon which I
Water heater repair
Trane 4WCX3060A1000BA Serial #135010319L. Met with and confirmed work to be completed. Proceeded to roof unit and carfully removed and installed the new defrost control board and tested. I also removed to clean the entire blower motor and assembly, taking apart the wheel and motor and cleaned thoroughly and applied antimicrobial to treatment before reassembling blower assembly and putting all back together to further test. System is operating properly now.
Perform diagnostic on a package heat pump system. Find defrost control board is bad and need to be replaced.