Adam installed my system in 2011 and has provided seasonal inspections and tune-ups on numerous occasions. Our system has continued to function at a high level while providing us savings over our previous system.
We asked Interstate to come in and do a post-Construction clean-up on a clients ventilation system and they did a fantastic job. Thanks so much :)
Timely, professional, and knowledgeable.
Great, speedy service and excellent advise regarding my aging HVAC system
Crew arrived on time and explained what they were going to do and how long it will take. No attitude no hassle
Isaac was extremely professional and provided exceptional service! Thanks
We have been with Interstate many years and they have always done right by us. Have a maintenance plan that pays for the semi annual service calls and that really helps us keep up with things as needed. They are great about reminders and updating you when tech is in route. Really appreciate their service.
Duct clean home recently purchased by new home owner. Supplies in ceiling and return under air handler. 2019 Armstrong Air Heat Pump / Fan coil system.
Perform blue shield protection plan furnace maintenance to both systems, clean flame sensors, test ignitor, gas pressure and temperature rise in range
Dryer vent cleaning through attic
Preformed fall maintenance on a 2019 Carrier heat pump system
Amana heat pump fall maintenance
Air duct inspection for home to determine cause if allergens and poor air flow.
Perform silver club furnace maintenance, change filter, check, ignitor,gas pressure and temperature rise, clean flame sensor
Duct cleaning and duct inspection for home with flex ductwork in ceiling.
Trane heat pump and air handler tune up.
AC not cooling. Refrigerant leak in AC. Estimate for new AC System
Home inspection AC Service. AC system is overcharged. Refrigerant recovery. AC inspection
Armstrong air conditioner freezing up. System low on refrigerant and blower motor burned up. Install EasySeal leak stop, replace blower motor and add r22 refrigerant.
Armstrong AC not running. Fan runs and shuts off quickly. Dual capacitor swollen. Replace dual capacitor, wash AC coil and checked charge.
Coleman AC not keeping up. Trailer house coil and blower very dirty.
Carrier AC not cooling. Failed dual capacitor. Install new dual capacitor. Attic ventilation too small and return ducts undersized