Adam installed my system in 2011 and has provided seasonal inspections and tune-ups on numerous occasions. Our system has continued to function at a high level while providing us savings over our previous system.
We asked Interstate to come in and do a post-Construction clean-up on a clients ventilation system and they did a fantastic job. Thanks so much :)
Timely, professional, and knowledgeable.
Great, speedy service and excellent advise regarding my aging HVAC system
Crew arrived on time and explained what they were going to do and how long it will take. No attitude no hassle
Isaac was extremely professional and provided exceptional service! Thanks
We have been with Interstate many years and they have always done right by us. Have a maintenance plan that pays for the semi annual service calls and that really helps us keep up with things as needed. They are great about reminders and updating you when tech is in route. Really appreciate their service.
Performed blue shield protection plan air conditioner maintenance. Change all filters provided with service. Washed condenser. Test capacitor and motor amp draw. Test compressor amp draw. Refrigerant levels are in range. No water in auxiliary drain pans. Drain is clear. Cycled unit multiple times. All amp draw in range. System is cooling at this time. Suggest adding surge protector to furnace.
I arrived for a non member no cool call. I first spoke with the homeowner and found one system to come on and run for about 5 minutes and shut off. I inspected the indoor system and found the capacitors on the blower motor to be unreadable and leaking oil. I check the blower motor and for the bearings to be in good condition but the back bearing is leak some oil. I gave the homeowner options on replacing the capacitor or the motor at this time. We decided to repair the capacitor and see how the system is running. I inspected the evaporator coil and found it to be clean but rusted. I inspected the condenser and found the the condenser coil to be stopped up. I clean the condenser and checked the systems operation. I found the contactor to be black and pitted. I also found the system to be running low on refegerant charge. I gave options on replacing the contactor and charging the system. We decide to add what refegerant was needed to get the system running properly. I added 3 LBS 12OZ of
06-10-2020 Jake Kring. I arrived for a non member no cool call. I first spoke with the homeowner and found that the smaller system is running but not cooling. I was also told that the main system has cot fire and will not turn on. I inspected the 1 1/2 ton system and found it to be a 18 year old Goodman system. I found this system to be completely frozen over. We will have to come back and inspect the system once it is defrosted. I looked at the main system and found the the air handler to have cot fire and burnt the main control board and the heat strip assembly. There is no model and serial numbers on this system. I research the heat strip kit and found it to go to a nordyne unit. I can only assume the air handler to be a nordyne unit. I inspected the condenser and found the no apparent issue at this time. The home is a 2400 sq ft home with a total of 4 1/2 tons of air. This home needs 6 tons of air to properly heat and cool this home. We also found the the water heater to be leaking
I arrived for a on member no cool call. I first inspected the furnace and found the control board to be burnt and not calling for the blower motor to run. I recommend to replace the control board. We decide to replace the control board and see how the system operates. I replaced the control board and checked the condensers operation. I found the system to be running low on r22. We decided to top off the system to get it in proper running condition. This system is now running to the best of its abilities at this time.
Inspect bathroom duct where odor was strongest. Found decaying animal material about 6â€ in on 2â€ wide duct in bathroom floor. With customer approval, uses 2â€ hose and camera to vacuum out source material as best as possible and fog in enzyme treatment for 5 minutes. Homeowner noticed immediate improvement in air quality. Talked about hydroxyl treatment as well, and homeowner will call us back if they decide the enzymes are not working fast enough. Remove decaying animal
Arrived to no cool service call performed system evaluation. Found microchannel condenser coil very clogged with debri. Used coil cleaner and deep cleaned coil got it as clean as possible. System was over charged some. Adjusted refrigerant levels. Freon pressure is a lot more in range now. Unit not tripping on high pressure at this time. If this does not fix problems with system I will have to suggest condenser replacement due to microchannel coil only being able to be serviced so much due to design. System is cooling at this time. Customer wants to see what happens with system before making any repair or replacement decisions. System cooling at this time.
I came out for a no cool. I checked the system over and found the condenser fan motor completely locked up. With approval, I installed a new universal condenser fan motor and new dual capacitor. I also washed the condenser coil. He signed up on the white service plan. And I waved the diagnostic fee, for today, because he signed up on the shield plan. I cycled the ac and checked all operations. All working at this time.
Duct clean home recently purchased by new home owner. Supplies in ceiling and return under air handler. 2019 Armstrong Air Heat Pump / Fan coil system.
Perform blue shield protection plan furnace maintenance to both systems, clean flame sensors, test ignitor, gas pressure and temperature rise in range
Dryer vent cleaning through attic
Preformed fall maintenance on a 2019 Carrier heat pump system
Amana heat pump fall maintenance
Air duct inspection for home to determine cause if allergens and poor air flow.
Perform silver club furnace maintenance, change filter, check, ignitor,gas pressure and temperature rise, clean flame sensor
Duct cleaning and duct inspection for home with flex ductwork in ceiling.