Timely, professional, and knowledgeable.
Great, speedy service and excellent advise regarding my aging HVAC system
Crew arrived on time and explained what they were going to do and how long it will take. No attitude no hassle
Isaac was extremely professional and provided exceptional service! Thanks
We have been with Interstate many years and they have always done right by us. Have a maintenance plan that pays for the semi annual service calls and that really helps us keep up with things as needed. They are great about reminders and updating you when tech is in route. Really appreciate their service.
Jordan is always professional and Friendly every time he shows up to do the routine heat and air system maintenance at my house. if bonuses are given out, I would surely recommend he receive one.
I’ve used Interstate Heat and Air for 7 years. Since they installed my system in 2010, they have always provided professional, timely service twice a year to ensure my system was running optimally. My technician this time, Johnny, was very professional, thorough, and right on time. I highly recommend this company for your heat and air needs.
Jordan arrived on time and did an excellent job. I highly recommend Interstate H & A
Armstrong AC not cooling properly. Capacitor needs to be replaced. Capacitor replacement and filter replacement
Bryant thermostat not working. Won't bring system on. Install new Honeywell T6 thermostat.
Armstrong AC not cooling. Add r22 refrigerant, changed dirty filters and clean evaporator coil
2 year old carrier infinity system not cooling. Install blower door correctly.
Perform an air conditioning tune up on the Bryant air conditioner. Wash out the condenser coil, check the R22 pressures
Inspect Carrier Infinity Hybrid heating and cooling system for optimal summer cooling performance. Also tune up 2.5 ton carrier air conditioning system for upstairs cooling needs.
Install new Honeywell thermostat
Install new carrier 3 ton complete system
Upstairs AC not cooling. Control Board Failure. Control board replacement
Serviced and charged a Goodman system for summer maintenance
Duct cleaning and furnace inspection
Cleaned drain and charged unit with r410a refrigerant
Carrier heat pump AC tune up.
Duct repair and duct cleaning for floor ducts.