Brandon was very knowledgable and professional.
Asked customer about filter and replaced 20x30 pleated filters with blue SPP. Asked about furnace access, and used 8 ft ladder to gain access in kitchen. Checked blower, amp draws. Checked evap coil, condensate line and float switch / drain pan. Condensate line is impossible to check last joint on, so ran system with 4 gallons of water to ensure it is in fact draining properly. Drain pan shows rust signs of previous condensate overflow. Checked level of evap coil, and made sure slope went towards main drain out. Checked surge protector previously installed and it is functional still. Checked ductwork and suystem looks to be low on return air, recommend increasing 16â€ flex duct to 20â€. Asked about surge protector recommendation from last time for condenser and hot water tank. Customer will have hwt drained with fall tune up. Washed condenser thoroughly, checked dual capacitor. Cycled system in and checked amp draws, contactor,fan, compressor and volts. Fan amps are running a bit hig
Perform non club tuneup to both systems. Washed condensers. Customer changes filters regularly. Blower and evaporator are clean. Drains are clear. Test all capacitors and motor amp draw. Test compressor amp draw. Refrigerant levels are in range for current temperatures. Both systems are cooling at this time. Found downstairs system to be a 4 ton system running at 880cfm of return. System this size requires 1600 cfm of air. Suggest adding another 16 duct return to system. Upstairs system also short on return air but customer does not use this system much and customer will consider work to upstairs unit. Gave duct price to downstairs unit. Both systems are cooling at this time.
Customer has trailer unit and trailer water heater. Took pictures and measurements will get pricing and availability thru a few vendors for equipment and follow up with customer.
Performed silver club furnace maintenance change filters, clean flame sensors, gas pressure and temperature rise in range
AC tune up on Goodman AC. Capacitor needs to be replace. Contactor has failed. AC repair
Air Conditioning Tune up, clean and test 6 Rheem package units for a shopping center. Shops include dog grooming, hair salon and fitness center.
AC maintenance on a 2008 Carrier system
AC repair, found clogged drain line on a 2011 Lennox system. Unclogged drain line and system is working properly
Cleaned system and tested all components to trane furnace
Duct cleaning and video inspection of underground air ducts.
Furnace tune up
Carrier ac tune up
Lennox AC maintenance
Furnace tune up