This is a top shelf Heat & Air company that I’ve used for several years. They are always there at designated time and the technicians are very knowledgeable and professional. You can’t go wrong with these guys.
Inspect home with two stories and two systems for duck cleaning, air mediation from nicotine smoke, and any other air quality issues. Customer also interested in talking about thermostat replacement. Looked over both systems, ductwork, ductwork composition and air quality options. The major issue with the downstairs system is that the old mylar return that has deteriorated to the point of letting in attic air. Recommend replacing ductwork, this involves moving the flu pipe for the furnace and the hot water tank in the garage and building a custom Plenum to attach to. Also talked about blowing in the attic insulation and remediating home with hydroxyl treatment for three days. Customer will look into thermostat options at a future date. is interested in Honeywell and nest programmable products. Customer will also look into having air ducts cleaned at a future date.
Performed blue shield protection plan air conditioner maintenance. Changed filters. Cleaned condenser. Test capacitor and motor amp draw. Compressor amp draw in range. Refrigerant levels are in range. System is cooling at this time.
Silver club Heating tune up on 2013 Carrier 80% furnace. Asked customer about hot and cold spots, how temperatures are keeping up and if they had turned on the furnace yet this season. Inspect Filters and they need to be changed in October. Home is heating and cooling well and furnace has not been turned on yet. Opened up furnace access panels and cleaned flame sensor. Cycled system on heat mode for a system precheck. Cycled system off and tested blower capacitor. Removed blower and checked wheel and heat exchanger. Checked flue. Checked evaporator coil and supply ductwork. Checked return ductwork and it could use a cleaning. Cycled system on and checked hot surface igniter, blower amps and inducer amps. Blower wheel is in range but running a little high at 10.4 amps, The returns are slightly undersized for the system and the filters are 2/3 used, so this may be why. Tested gas pressure and reset gas plug. Checked temperature rise and indoor delta t. System is heating properly!at this
Came out to call. Customer stated AC wasnâ€™t cooling properly. I checked system over and found the capacitor had gone out. I discussed with customer customer repair needed and pricing. Capacitor is under warranty, but labor isnâ€™t. I replaced the capacitor and cycled system on. I found the AC to be low on refrigerant. System is running at a 4 degree subcooling and it needs to be ten. I added 1.6lbs of 410a to get proper subcooling. System is cooling properly at this time. I recommended customer replace coil in attic seeing there could be a possible leak in it.
Serviced a carrier furnace for winter operation.
Dryer vent inspection and cleaning
Replaced a capacitor on a Armstrong system.
Test capacitor and motor amp draw, compressor amp draw, refrigerant levels to 2005 concord air conditioner
2007 Goodman Air Conditioner and 2013 RUUD Furnace summer preventative maintenance plan.
Added refrigerant to carrier air conditioner
Cleaned system and tested all components to American standard air conditioner
Fixed Ruud ac and preformed maintenance
Replace control board to carrier furnace
Repair refrigerant leak and charge system
Estimate to replace complete system