Joe went out of way to take care of our smoke alarm dilemma
Although we had an appointment time miscommunication tech was nothing but pleasant and helpful.
Terrific, knowledgeable technicians - thank you for the professional and speedy services.
Amazing service! Accommodated our need for a 5am (!) service call to troubleshoot our fire alarm system. Terrific all the way around - from Jeff in scheduling to Dakota and partner on the service call. Thanks very much.
Super speedy and knowledgeable! Thank you!
Punctual, skilled and thorough!
United Fire recently completed fire alarm, sprinkler and backflow inspections at our commercial office property. They are "attention to detail" people and all of the staff provided good Customer Service. Reports were ready on the same day as the inspection!
This is the second year Jason has completed the annual fire alarm/sprinkler system test for our building. He is terrific! Very knowledge and explains things very thoroughly. Absolute A+ service.
INSTALL NEW DRY VALVE RESTRICTOR ASSEMBLY
CAP OFF SPRINKLER HEAD FOR REMODEL - 1 2. LABOR 3. SERVICE CALL
1. 5 YEAR INTERNAL SPRINKLER MAINTENANCE 2. PROVIDE WRENCH FOR SPARE HEAD BOX 3. LABOR 4. SERVICE CALL
Fire extinguisher annual maintenance
. ANNUAL WET SPRINKLER INSPECTION 2. ANNUAL FIRE ALARM INSPECTION AND TEST 3. ANNUAL FIRE EXTINGUISHER INSPECTION 4. LABOR 5. SERVICE CALL
20 1.25 Fire extinguisher annual maintenance PLEASE REMOVE 1 AMEREX B-402 FROM INVENTORY AS I SWAPPED OUT AN EXTINGUISHER THAT NEEDED RECHARGED FOR A NEW ONE
Portable Extinguishers Inspection
ANNUAL SPRINKLER INSPECTION
Sprinkler Annual EXT Fire extinguisher annual maintenance EE Emergency / Exit Light Inspection
Fire Sprinkler Emergency: Possibly leaking sprinkler pipe. Please investigate. Pictures attached to job
REMOVE AND REPLACE DRY SPRINKLER HEADS OVER 10 YEARS OLD
REPLACE SMOKE DETECTORS NOT COMPATIBLE WITH CURRENT ALARM PANEL REPLACE FAILED ALARM PANEL BATTERIES, Test top of shaft smoke detector - customer coordinated with elevator company