They did a great job on my duct service cleaning. Would definitely recommend!
Jordan was amazing thank you so much for your help. Great experience
I came out for an ac maintenance. I washed the condenser coil. I checked the blower, drain, filters, ductwork, evap coil, capacitor, contactor and all wiring. I cycled the ac and checked all temps, amps and charge. All working properly.
Came out to call. Customer said system was freezing up and not cooling. I checked system over and found the blower severely clogged, which was causing the system to not pull enough air through the coil. Customer said that it was supposed to be cleaned as part of the install. I pulled the blower, cleaned it thoroughly and reinstalled it. Turned system on and checked pressures to verify system was working properly. System is now cooling properly within manufactured specifications.
Came out to do maintenances on 3 systems. Gave customer filters that she will change herself inside the home. I performed preventative maintenances on 3 Carrier units. I started with the 2 5 ton Carriers that supply the upstairs and downstairs of home. Checked thermostat operation, wiring, compressors, contactors, capacitors, fan motors, and overall condition of condenser units. I recommended capacitor be replaced on downstairs unit, seeing it was well below 10% of the recommended rating. Customer had me replace it. I washed condenser coils thoroughly, and checked temperatures and pressures of condensers. I did the same for the carrier unit supplying the shop they had in back. All three systems are cooling properly within manufactured specifications at this time.
Came out to call. Customer said system was making a weird noise yesterday. They have had the system off since then I checked system over and found it to be running properly. I checked and tested the amps, temperatures and pressures of condenser to verify system was cooling properly. System was dirty, so I washed it. I recommended maintenance plan to help keep system clean and run efficiently throughout the year. Customer signed up for red plan.
Duct cleaning from previous tune up estimate. Layed drop sheets where necessary. Remove vents grills and old filters and clean with dry spinning brush. Use 8ft and 4ft ladders to reach and clean 16 supplies and 3 returns. Clean supplies with 2 to 6 passes each and clean returns with 2 to 4 passes each. Replace vents, grills and fresh customer supplied filters. Sprayed in hospital grade disinfectant spray. Picked up drop sheets and cleaned up excess debris. Ducts are thoroughly clean at this time! See attached before and after photos of cleaned return and supply duct.
Performed preventative maintenance on AC split system heat pump. System is an 11 year old Trane unit. I did a thorough inspection of the air handler and ductwork. Inspected blower assembly, electrical components, wiring, evaporator coil, drain, and duct work. Checked thermostat operation, capacitors, contactor, compressor, fan motor, amps, temperatures and pressures of condenser. Overall system is operating and cooling properly within manufactured specifications. I discussed with customer about duct cleaning and the price to do it. Customer had me set up an appointment to have it done.
Gave estimate for a 4 ton HP and coil. Install a new stat and shorten crossover duct. Denied financing.
I came out for a no cool, on the upstairs system. I. Necked the ac over and found the dual capacitor at almost 0. The system is still under a parts warranty. I installed a new warranty dual capacitor. She cycled the ac, from the thermostat, and I checked all operations and charge. All working well. Sheâ€™s already scheduled to have us out in a few weeks to do the ac maintenance, so I didnâ€™t wash the ac coil today.
Inspected two trane air handler and heat pumps. Installed two uv lights.
Preventative Maintenance Service on 11 year old Trane Residential Furnaces. Igniter and Capacitor Replacement Recommendation
Serviced a amana furnace for winter performance
Lennox heat pump and Goodman air handler fall maintenance
Duct cleaning home built in 2007
AC repair, cleaned extremely dirty evaporator coil on a 2016 Carrier system. System is working properly at this time
Ruud AC not cooling 3 amp fuse blown. Replace fuse, wash condenser coil and check refrigerant charge.