Very professiinal and knowegeable.
Great job friendly nice to talk to
This company had me at hello. Our first interaction was 9 years ago, middle of August and our capacitor went out. We called, they set it up, Kai (the owner himself) came out and made the repair. We signed up for the silver service for $19.99 a month to maintain our unit and get us a discount on any services or repairs. Every technician we’ve had our has been professional, kind and very knowledgeable. Never a bad experience and seem to always go above and beyond to make sure we are satisfied.
Silver Club AC tune up visit. Inspect and asked about how AC is running. Washed condenser, checked dual capacitor. Checked blower, evap coil and condensate line. Checked float switch and drain pan. Changed customer supplied filter and informed customer they have a spare fresh 20x25 filter in attic. Cycled system on and checked blower, fan and compressor amps. Checked contactor and volt drop. Checked refrigerant pressure and outside delta t. System is running great at this time! Talked to customer about our duct cleaning services.
Arrived to no cool service call and performed system evaluation on 2012 carrier condenser. Found bad dual capacitor. Spoke with homeowner. Install a new dual capacitor. Tested amp draw. Tested refrigerant levels. Amp draw in range. Refrigerant levels are in range. System is cooling at this time. Suggest regular maintenance to keep system running as designed. Customer declined to have furnace and coil looked at at this time.
Dryer vent cleaning through attic. Roof has a steep Sloan and 4â€ dryer exhaust vent is venting from an 8â€ attic air vent, instead of a 4â€ dryer dampered vent. Recommend having a roofer place the proper type of vent. Inspect vent with camera and after inspecting attic space found that vent is approximately 28 feet in length with 5 turns, and is completely backed up throughout. Cleaned from below with 8 passes and from above in attic crawlspace with 3 passes. Cleaned up excess debris, Reconnected vent by strapping to attic air opening and reconnect new dryer and cycled system on to ensure proper operation. Dryer is operating well at this time.
Carrier propane furnace preventative maintenance
Serviced a carrier system for summer preformed. Bid duct cleaning for downflow system.
Carrier 14 SEER Air conditioner maintenance with Silver club plan.
Serviced a carrier system and a mini split for summer performance. Wash out condenser and change filterss.
Perform a tune up on the Ruud air handler and heat pump. Check all capacitors, motors refrigerant pressures. Install a hard start kit on the Copeland compressor
AC repair, found a failed compressor
Charged a train system for summer performance.
Amana heat pump not cooling well. Found reversing valve leaking.
Inspect Lennox air conditioners upstairs and downstairs for summer reliability.
Duct cleaning after water back up in floor ducts. Home remediation
Replace high pressure switch to carrier mini split
Tested components to Carrier minisplit