Brandon is a top-notch technician. He knows his business, cares about the satisfaction of the customer, and goes beyond the normal expectations to provide that satisfaction. Having once been an A/C service technician myself, I know what to look for, and I saw it all in Brandon. Interstate installed my system in 2012 and today was the first time I had any trouble ever. The condenser fan motor bushings finally wore out, and I know that kind of longevity is unusually good. Maybe I can get another 8 yrs from the new one!
I have used Interstate Heat/Air for several years. I have never been disappointed. They are professional and helpful. Adam was no different. They perform maintenance on my heating and air unit twice a year. if something needs attention, they fix it, but they don't try to talk you into anything that isn't broken. Today was a great day. Everything was fine. I have them replace my filters. They are always willing because I am too old and short to try.
Randy was very professional. He did an excellent job, suggested a couple of things, but was not pushy. I have always been pleased with technicians from Int H/A
Always do a great job and are true professionals
Excellent job by Adam. Very professional and got the job done in a timely manner. Thanks!
Arrived to service call performed system evaluation. Found condenser fan motor with bad bearings. Motor over amping and leaking oil. Spoke to customer. Customer chose to replace motor. Installed 825 rpm motor. Installed new compressor capacitor and fan capacitor. Tested amp draw. Amp draw in range. Refrigerant levels are in range. Condenser is clean. Customer is retired and on fixed income gave discount to help customer. System is cooling at this time.
I arrived for a non membership no cool call. I first spoke with the tenets and found the main issue to be the outdoor system is tripping the breaker. I checked the condenser and found the the compressor to be I internally shorted. I inspect the indoor system location in the attic and found the duct to be in poor condition due to animals tearing up the insulation and duct. I contacted the homeowners and we talked about replacement of the system with a unit that they have in storage. I told the homeowner that that the cost to install a used system would be a time and material charge if they have a comparable system. We are to hear from the homeowners once they find out what size system they have in storage.
I came out for a no cool. They said the system has been down for a but, probably since the storms a few days back. I checked the system over and found one of the fuses, in the disconnect, blown. With approval I picked up 2 new 80A fuses and installed the . I left the 1 fuse that was still good in the disconnect box. I megaohmed the compressor and motors. All checked out ok. I cycled the ac and checked all operations. All working well.
I arrived for a silver member ac pm. The homeowner did not want us in the house due to covid-19 issue at this time. I was not able to inspected the indoor system due to this. I gave the homeowner a free filters so I knew that the filters were clean and the indoor system was getting the best air flow with out me inspecting the indoor system. I inspected the condenser and found vines and other debris clogging up the condenser. I removed all heavy debris from the condenser coil and cleaned the coils free of all other debris. I found ants in and around the condenser. I made the homeowner aware of this and I recommend to have some ant killer put around condenser and house to help prevent a breakdown in the future.
Perform red shield protection plan air conditioner maintenance
Duct cleaning home with 7 supplies and 2 returns.
Trane heat pump pack unit not heating. Fuse blown from power surge. Replace fuse and check system operation
Perform silver club furnace maintenance, change filters, check capacitor and motor amp draw, gas pressure and temperature rise in range
Duct cleaning new home purchase of home built in the 1950s with floor ducts.
Trane fall furnace tune up. Replace pleated filters.
Duct cleaning and in- ground duct repair from concrete slab fill sand in the vents.
Under slab construction air duct repair work.
System tune up for summer air conditioning. York 3 ton system is operating very well. Inspect ductwork and attic insulation for better cooling capability.
Charged and serviced carrier condenser and amana furnace