The team did a very good job from start to finish. Professional, prepared and organized through the whole installation process. Hats off to Hobaica installation team today.
Ethan is a great worker and he kept us in the loop all day long.
Good product and good people
Bihn is experienced, capable and considerate. Always a pleasure
We had our complimentary 2 year air conditioning warranty service done by Mike. He was very helpful & answered all of our questions. This company goes above & beyond and Mike did the same today.
Great service and attitude.
Hobaica’s technician, Mike Varela, inspected our air conditioner units. He did a very thorough job, and gave us a complete inspection report. We have been customers of Hobaica for two years, and are very pleased with their professionalism, knowledge, and customer service.
New wine system installed by Jorge and Troy
Line system start up dial-in refrigerant pressure compressor amperage is blower motor all operating and cooling properly now
Daikin start assist
New wine system installed by Jorge, jason and troy
Maintenance on Trane split heat pump
I removed the leaking water heater and install the new 50 gallon electric tall water heater in the garage. I fixed the improper temperature and pressure relief line that 90 straight Up and then back down and out the wall.
Wine cellar repair
Performed water heater flush and safety inspection on 2015 50 gallon short electric Ruud water heater in the garage. Flushed down tank completely and rinsed in some more cold water to stir up sediment and debris and flushed again. Tank does show some rust on the cold water inlet as well as around bottom of tank, none is leaking now. Water heater is back up and heating properly now.
Found the suction line 90° elbow at the compressor suction line is leaking refrigerant and hissing out. Repair will entail refrigerant recovery, vacuum pump usage, welding and new liquid line filter and all new refrigerant 10lbs r410a. The repair is covered under one year labor warranty from the compressor replacement. I recovered the remaining Refrigerant and welded closed the leak and replaced the liquid line filter while flowing nitrogen. I pressure tested and checked for
Tcc gold maintenance
Customer reported system is only working half speed for the air-conditioning and not totally maintaining the temperature on the extreme heat days
Units ANNUAL TCC GOLD 7 UNITS & 1 WINE SYSTEM BI-ANNUAL INSPECTION & ELECTRICAL INSPECTION (8AM) point of contact is Owner to be let inside guard gate and check the air conditioning and refrigeration systems for the summer maintenance schedule and probably the air filters are dirty
Customer report new one system is leaking something. I will ask him if it’s leaking water, oil on refrigerant or none of the above because I’m not sure
In Scottsdale Az, performing a promotional HVAC inspection on a 2002 Trane PKG heat pump. I checked thermostat function, checked indoor temps, indoor motor amp draw and tested its capacitor which is testing outside the 10% loss range. No action was taken for this capacitor today, there are electrical issues with low and high voltage wiring which has been shared and shown to Stephanie. A request for quote has Been scheduled today for 3-5pm with Andy H. Unit is operating at this time! Thank you!